| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 4289.020 | 4289.020 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 4289.02 | 4289.02 | 0.138394 | 14.23 | 8.42 | 0.00620074 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 7.6729 | 21.10 | 0.00730659 | 37.6560 | 1402.05 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 1990.921 | 1594.041 | 0.120272 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 11:00:00 | 2262.67 | 2262.67 | 0.120272 | 24.71 | 14.31 | 0.00846786 | 11.60 | 9.59 | 0.00846786 | 33.00 | 0.00686230 | 15.70 | 8.8290 | 23.89 | 0.00862844 | 37.4671 | 1122.92 | 0.00 | 1987.75 | 1434.62 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 3781.201 | 3781.201 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3781.20 | 3781.20 | 0.120272 | 14.24 | 8.42 | 0.00620333 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 8.8290 | 21.10 | 0.00730759 | 37.6611 | 1404.29 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 3781.201 | 3781.201 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3781.20 | 3781.20 | 0.120272 | 14.24 | 8.42 | 0.00620333 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 8.8290 | 21.10 | 0.00730759 | 37.6611 | 1404.29 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 2405.417 | 1925.910 | 0.145311 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 2705.11 | 2655.63 | 0.145311 | 25.50 | 14.70 | 0.00862838 | 11.60 | 9.62 | 0.00850000 | 33.00 | 0.00686230 | 15.70 | 17.7299 | 23.89 | 0.00900899 | 39.0995 | 1292.08 | 0.00 | 2401.58 | 1733.30 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 5068.276 | 5068.276 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 5068.28 | 5068.28 | 0.145311 | -3.21 | -3.21 | 0.00366557 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 17.7299 | 21.11 | 0.00800000 | 41.1698 | 961.45 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 5068.276 | 5068.276 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 5068.28 | 5068.28 | 0.145311 | -3.21 | -3.21 | 0.00366557 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 17.7299 | 21.11 | 0.00800000 | 41.1698 | 961.45 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 1935.217 | 1549.442 | 0.116906 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | 2157.40 | 2149.08 | 0.116906 | 24.51 | 14.29 | 0.00852516 | 11.60 | 9.62 | 0.00850000 | 30.87 | 0.00686230 | 15.03 | 8.9144 | 23.89 | 0.00868791 | 37.7229 | 981.32 | 0.00 | 1932.13 | 1394.48 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 3679.011 | 3679.011 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3679.01 | 3679.01 | 0.116906 | 10.57 | 6.36 | 0.00572265 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 8.9144 | 21.11 | 0.00745643 | 38.4131 | 898.06 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 3679.011 | 3679.011 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3679.01 | 3679.01 | 0.116906 | 10.57 | 6.36 | 0.00572265 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 8.9144 | 21.11 | 0.00745643 | 38.4131 | 898.06 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 1644.761 | 1316.886 | 0.099360 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | 1776.95 | 1769.31 | 0.099360 | 24.24 | 14.20 | 0.00852758 | 11.60 | 9.62 | 0.00850000 | 27.22 | 0.00686230 | 13.83 | 10.4887 | 23.89 | 0.00872272 | 37.8726 | 826.50 | 0.00 | 1642.14 | 1185.18 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 3187.363 | 3187.363 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3187.36 | 3187.36 | 0.099360 | 10.60 | 6.38 | 0.00572787 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 10.4887 | 21.11 | 0.00745768 | 38.4195 | 900.30 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 3187.363 | 3187.363 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3187.36 | 3187.36 | 0.099360 | 10.60 | 6.38 | 0.00572787 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 10.4887 | 21.11 | 0.00745768 | 38.4195 | 900.30 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 2991.667 | 2395.294 | 0.180727 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 3380.80 | 3369.39 | 0.180727 | 25.21 | 14.52 | 0.00852295 | 11.60 | 9.62 | 0.00850000 | 33.00 | 0.00686230 | 15.70 | 14.5253 | 23.89 | 0.00880516 | 38.2254 | 1458.72 | 0.00 | 2986.90 | 2155.74 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 6079.900 | 6079.900 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 6079.90 | 6079.90 | 0.180727 | 9.99 | 5.98 | 0.00560645 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 14.5253 | 21.11 | 0.00742870 | 38.2727 | 2143.27 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 6079.900 | 6079.900 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 6079.90 | 6079.90 | 0.180727 | 9.99 | 5.98 | 0.00560645 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 14.5253 | 21.11 | 0.00742870 | 38.2727 | 2143.27 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 2159.640 | 1729.127 | 0.130464 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | 2436.25 | 2436.25 | 0.130464 | 24.56 | 14.27 | 0.00848152 | 11.60 | 9.61 | 0.00848152 | 32.09 | 0.00686229 | 15.41 | 8.1393 | 23.89 | 0.00861548 | 37.4115 | 1240.40 | 0.00 | 2156.20 | 1556.20 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 4066.812 | 4066.812 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 4066.81 | 4066.81 | 0.130464 | 14.22 | 8.41 | 0.00619979 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 8.1393 | 21.10 | 0.00730623 | 37.6541 | 1401.23 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 4066.812 | 4066.812 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 4066.81 | 4066.81 | 0.130464 | 14.22 | 8.41 | 0.00619979 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 8.1393 | 21.10 | 0.00730623 | 37.6541 | 1401.23 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 1805.626 | 1445.684 | 0.109078 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 11:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | 1991.60 | 1991.60 | 0.109078 | 24.44 | 14.21 | 0.00846136 | 11.60 | 9.59 | 0.00846136 | 29.50 | 0.00686230 | 14.59 | 9.7351 | 23.89 | 0.00864095 | 37.5209 | 1031.44 | 0.00 | 1802.75 | 1301.10 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 3467.531 | 3467.531 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3467.53 | 3467.53 | 0.109078 | 14.24 | 8.42 | 0.00620239 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 9.7351 | 21.10 | 0.00730723 | 37.6592 | 1403.47 | 0.00 | -999.00 | -999.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 3467.531 | 3467.531 | -999.0 | -999.0 | -999.000 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3467.53 | 3467.53 | 0.109078 | 14.24 | 8.42 | 0.00620239 | 50.00 | 21.21 | 0.00800000 | -18.80 | 0.00088830 | -18.80 | 9.7351 | 21.10 | 0.00730723 | 37.6592 | 1403.47 | 0.00 | -999.00 | -999.00 |
Report: Coil Sizing Details
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Coils| Coil Type | Coil Location | HVAC Type | HVAC Name | Zone Name(s) | System Sizing Method Concurrence | System Sizing Method Capacity | System Sizing Method Air Flow | Autosized Coil Capacity? | Autosized Coil Airflow? | Autosized Coil Water Flow? | OA Pretreated prior to coil inlet? | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Terminal Unit Reheat Coil Multiplier | DX Coil Capacity Increase Ratio from Too Low Flow/Capacity Ratio | DX Coil Capacity Decrease Ratio from Too High Flow/Capacity Ratio | Moist Air Heat Capacity [J/kg-K] | Dry Air Heat Capacity [J/kg-K] | Standard Air Density Adjusted for Elevation [kg/m3] | Supply Fan Name for Coil | Supply Fan Type for Coil | Supply Fan Maximum Air Volume Flow Rate [m3/s] | Supply Fan Maximum Air Mass Flow Rate [kg/s] | Plant Name for Coil | Plant Fluid Specific Heat Capacity [J/kg-K] | Plant Fluid Density [kg/m3] | Plant Maximum Fluid Mass Flow Rate [kg/s] | Plant Design Fluid Return Temperature [C] | Plant Design Fluid Supply Temperature [C] | Plant Design Fluid Temperature Difference [deltaC] | Plant Design Capacity [W] | Coil Capacity Percentage of Plant Design Capacity [%] | Coil Fluid Flow Rate Percentage of Plant Design Flow Rate [%] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Total Ideal Loads Peak | Date/Time at Total Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Off-Rating Capacity Modifier at Ideal Loads Peak [ ] | Coil Air Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Coil Leaving Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Plant Fluid Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Entering Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Leaving Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Plant Fluid Temperature Difference at Ideal Loads Peak [deltaC] | Supply Fan Air Heat Gain at Ideal Loads Peak [W] | Coil and Fan Net Total Capacity at Ideal Loads Peak [W] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | System Return Air Drybulb at Ideal Loads Peak [C] | System Return Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | Coil Air Mass Flow Rate at Rating Conditions [kg/s] | Coil Entering Air Drybulb at Rating Conditions [C] | Coil Entering Air Wetbulb at Rating Conditions [C] | Coil Entering Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Rating Conditions [J/KG-K] | Coil Leaving Air Drybulb at Rating Conditions [C] | Coil Leaving Air Wetbulb at Rating Conditions [C] | Coil Leaving Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Leaving Air Enthalpy at Rating Conditions [J/KG-K] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 12KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 3659.918 | 2930.333 | 0.221096 | -999.0 | -999.000 | -999.0000 | 1.13601 | 1.00000 | 1020.6846 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.221096 | 0.21337535 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS WB=>MDB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 4144.81 | 4130.33 | 0.8830 | 0.21337535 | 0.221096 | 24.97 | 14.44 | 0.00852343 | 46803.2 | 11.60 | 9.62 | 0.00850000 | 33096.3 | -999.0 | -999.00 | -999.00 | -999.00 | 256.748 | 3888.06 | 33.00 | 0.00686230 | 15.70 | 0.02625116 | 11.8732 | 23.89 | 0.00874723 | 23.89 | 0.00874723 | 37.9773 | 1832.01 | 0.00 | 3654.08 | 2637.27 | 0.20492750 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 7211.043 | 7211.043 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.221096 | 0.21337535 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 7211.04 | 7211.04 | 1.0000 | 0.21337535 | 0.221096 | 10.05 | 6.02 | 0.00561871 | 24255.5 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 7211.04 | -18.80 | 0.00088830 | -18.80 | 0.02625116 | 11.8732 | 21.11 | 0.00743162 | 21.11 | 0.00743162 | 38.2876 | 2155.27 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 7211.043 | 7211.043 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.221096 | 0.21337535 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 7211.04 | 7211.04 | 1.0000 | 0.21337535 | 0.221096 | 10.05 | 6.02 | 0.00561871 | 24255.5 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 7211.04 | -18.80 | 0.00088830 | -18.80 | 0.02625116 | 11.8732 | 21.11 | 0.00743162 | 21.11 | 0.00743162 | 38.2876 | 2155.27 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 2290.905 | 1834.225 | 0.138394 | -999.0 | -999.000 | -999.0000 | 1.18323 | 1.00000 | 1020.6008 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.138394 | 0.13356106 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | 2585.40 | 2585.40 | 0.8861 | 0.13356106 | 0.138394 | 24.52 | 14.25 | 0.00847836 | 46227.1 | 11.60 | 9.60 | 0.00847836 | 33041.6 | -999.0 | -999.00 | -999.00 | -999.00 | 160.710 | 2424.69 | 32.09 | 0.00686229 | 15.41 | 0.01061882 | 7.6729 | 23.89 | 0.00861266 | 23.89 | 0.00861266 | 37.3994 | 1317.10 | 0.00 | 2287.25 | 1650.78 | 0.12827318 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 4289.020 | 4289.020 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.138394 | 0.13356106 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 4289.02 | 4289.02 | 1.0000 | 0.13356106 | 0.138394 | 14.23 | 8.42 | 0.00620074 | 29969.4 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4289.02 | -18.80 | 0.00088830 | -18.80 | 0.01061882 | 7.6729 | 21.10 | 0.00730659 | 21.10 | 0.00730659 | 37.6560 | 1402.05 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 4289.020 | 4289.020 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.138394 | 0.13356106 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 4289.02 | 4289.02 | 1.0000 | 0.13356106 | 0.138394 | 14.23 | 8.42 | 0.00620074 | 29969.4 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4289.02 | -18.80 | 0.00088830 | -18.80 | 0.01061882 | 7.6729 | 21.10 | 0.00730659 | 21.10 | 0.00730659 | 37.6560 | 1402.05 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 1990.921 | 1594.041 | 0.120272 | -999.0 | -999.000 | -999.0000 | 1.15857 | 1.00000 | 1020.5813 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.120272 | 0.11607183 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 11:00:00 | 2262.67 | 2262.67 | 0.8799 | 0.11607183 | 0.120272 | 24.71 | 14.31 | 0.00846786 | 46395.3 | 11.60 | 9.59 | 0.00846786 | 33015.1 | -999.0 | -999.00 | -999.00 | -999.00 | 139.666 | 2123.00 | 33.00 | 0.00686230 | 15.70 | 0.01061882 | 8.8290 | 23.89 | 0.00862665 | 23.89 | 0.00862844 | 37.4671 | 1122.92 | 0.00 | 1987.75 | 1434.62 | 0.11147637 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 3781.201 | 3781.201 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.120272 | 0.11607183 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3781.20 | 3781.20 | 1.0000 | 0.11607183 | 0.120272 | 14.24 | 8.42 | 0.00620333 | 29987.1 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 3781.20 | -18.80 | 0.00088830 | -18.80 | 0.01061882 | 8.8290 | 21.10 | 0.00730759 | 21.10 | 0.00730759 | 37.6611 | 1404.29 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 3781.201 | 3781.201 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.120272 | 0.11607183 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3781.20 | 3781.20 | 1.0000 | 0.11607183 | 0.120272 | 14.24 | 8.42 | 0.00620333 | 29987.1 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 3781.20 | -18.80 | 0.00088830 | -18.80 | 0.01061882 | 8.8290 | 21.10 | 0.00730759 | 21.10 | 0.00730759 | 37.6611 | 1404.29 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 8KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 2405.417 | 1925.910 | 0.145311 | -999.0 | -999.000 | -999.0000 | 1.08214 | 1.00000 | 1020.8797 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.145311 | 0.14023718 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS WB=>MDB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 2705.11 | 2655.63 | 0.8892 | 0.14023718 | 0.145311 | 25.50 | 14.70 | 0.00862838 | 47614.7 | 11.60 | 9.62 | 0.00850000 | 33096.5 | -999.0 | -999.00 | -999.00 | -999.00 | 168.743 | 2536.36 | 33.00 | 0.00686230 | 15.70 | 0.02576352 | 17.7299 | 23.89 | 0.00900899 | 23.89 | 0.00900899 | 39.0995 | 1292.08 | 0.00 | 2401.58 | 1733.30 | 0.13468498 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 5068.276 | 5068.276 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.145311 | 0.14023718 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 5068.28 | 5068.28 | 1.0000 | 0.14023718 | 0.145311 | -3.21 | -3.21 | 0.00366557 | 5915.6 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 5068.28 | -18.80 | 0.00088830 | -18.80 | 0.02576352 | 17.7299 | 21.11 | 0.00800000 | 21.11 | 0.00800000 | 41.1698 | 961.45 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 5068.276 | 5068.276 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.145311 | 0.14023718 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 5068.28 | 5068.28 | 1.0000 | 0.14023718 | 0.145311 | -3.21 | -3.21 | 0.00366557 | 5915.6 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 5068.28 | -18.80 | 0.00088830 | -18.80 | 0.02576352 | 17.7299 | 21.11 | 0.00800000 | 21.11 | 0.00800000 | 41.1698 | 961.45 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 1935.217 | 1549.442 | 0.116906 | -999.0 | -999.000 | -999.0000 | 1.19269 | 1.00000 | 1020.6879 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.116906 | 0.11282427 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS WB=>MDB 1 | 7/21 16:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | 2157.40 | 2149.08 | 0.8970 | 0.11282427 | 0.116906 | 24.51 | 14.29 | 0.00852516 | 46339.0 | 11.60 | 9.62 | 0.00850000 | 33096.3 | -999.0 | -999.00 | -999.00 | -999.00 | 135.758 | 2021.65 | 30.87 | 0.00686230 | 15.03 | 0.01042156 | 8.9144 | 23.89 | 0.00868791 | 23.89 | 0.00868791 | 37.7229 | 981.32 | 0.00 | 1932.13 | 1394.48 | 0.10835739 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 3679.011 | 3679.011 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.116906 | 0.11282427 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3679.01 | 3679.01 | 1.0000 | 0.11282427 | 0.116906 | 10.57 | 6.36 | 0.00572265 | 25048.3 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 3679.01 | -18.80 | 0.00088830 | -18.80 | 0.01042156 | 8.9144 | 21.11 | 0.00745643 | 21.11 | 0.00745643 | 38.4131 | 898.06 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 3679.011 | 3679.011 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.116906 | 0.11282427 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3679.01 | 3679.01 | 1.0000 | 0.11282427 | 0.116906 | 10.57 | 6.36 | 0.00572265 | 25048.3 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 3679.01 | -18.80 | 0.00088830 | -18.80 | 0.01042156 | 8.9144 | 21.11 | 0.00745643 | 21.11 | 0.00745643 | 38.4131 | 898.06 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 1644.761 | 1316.886 | 0.099360 | -999.0 | -999.000 | -999.0000 | 1.25546 | 1.00000 | 1020.6924 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.099360 | 0.09589050 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS WB=>MDB 1 | 7/21 10:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | 1776.95 | 1769.31 | 0.9256 | 0.09589050 | 0.099360 | 24.24 | 14.20 | 0.00852758 | 46066.6 | 11.60 | 9.62 | 0.00850000 | 33096.3 | -999.0 | -999.00 | -999.00 | -999.00 | 115.382 | 1661.57 | 27.22 | 0.00686230 | 13.83 | 0.01042156 | 10.4887 | 23.89 | 0.00872272 | 23.89 | 0.00872272 | 37.8726 | 826.50 | 0.00 | 1642.14 | 1185.18 | 0.09209405 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 3187.363 | 3187.363 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.099360 | 0.09589050 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3187.36 | 3187.36 | 1.0000 | 0.09589050 | 0.099360 | 10.60 | 6.38 | 0.00572787 | 25088.0 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 3187.36 | -18.80 | 0.00088830 | -18.80 | 0.01042156 | 10.4887 | 21.11 | 0.00745768 | 21.11 | 0.00745768 | 38.4195 | 900.30 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 3187.363 | 3187.363 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.099360 | 0.09589050 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3187.36 | 3187.36 | 1.0000 | 0.09589050 | 0.099360 | 10.60 | 6.38 | 0.00572787 | 25088.0 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 3187.36 | -18.80 | 0.00088830 | -18.80 | 0.01042156 | 10.4887 | 21.11 | 0.00745768 | 21.11 | 0.00745768 | 38.4195 | 900.30 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 10KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 2991.667 | 2395.294 | 0.180727 | -999.0 | -999.000 | -999.0000 | 1.11929 | 1.00000 | 1020.6837 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.180727 | 0.17441591 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS WB=>MDB 1 | 7/21 14:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 14:00:00 | 3380.80 | 3369.39 | 0.8849 | 0.17441591 | 0.180727 | 25.21 | 14.52 | 0.00852295 | 47048.6 | 11.60 | 9.62 | 0.00850000 | 33096.3 | -999.0 | -999.00 | -999.00 | -999.00 | 209.869 | 3170.93 | 33.00 | 0.00686230 | 15.70 | 0.02625116 | 14.5253 | 23.89 | 0.00880516 | 23.89 | 0.00880516 | 38.2254 | 1458.72 | 0.00 | 2986.90 | 2155.74 | 0.16751052 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 6079.900 | 6079.900 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.180727 | 0.17441591 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 6079.90 | 6079.90 | 1.0000 | 0.17441591 | 0.180727 | 9.99 | 5.98 | 0.00560645 | 24161.8 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6079.90 | -18.80 | 0.00088830 | -18.80 | 0.02625116 | 14.5253 | 21.11 | 0.00742870 | 21.11 | 0.00742870 | 38.2727 | 2143.27 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 6079.900 | 6079.900 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.180727 | 0.17441591 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 6079.90 | 6079.90 | 1.0000 | 0.17441591 | 0.180727 | 9.99 | 5.98 | 0.00560645 | 24161.8 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6079.90 | -18.80 | 0.00088830 | -18.80 | 0.02625116 | 14.5253 | 21.11 | 0.00742870 | 21.11 | 0.00742870 | 38.2727 | 2143.27 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 7KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 2159.640 | 1729.127 | 0.130464 | -999.0 | -999.000 | -999.0000 | 1.18032 | 1.00000 | 1020.6067 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.130464 | 0.12590822 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 16:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 17:00:00 | 2436.25 | 2436.25 | 0.8865 | 0.12590822 | 0.130464 | 24.56 | 14.27 | 0.00848152 | 46274.8 | 11.60 | 9.61 | 0.00848152 | 33049.6 | -999.0 | -999.00 | -999.00 | -999.00 | 151.502 | 2284.75 | 32.09 | 0.00686229 | 15.41 | 0.01061882 | 8.1393 | 23.89 | 0.00862514 | 23.89 | 0.00861548 | 37.4115 | 1240.40 | 0.00 | 2156.20 | 1556.20 | 0.12092333 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 4066.812 | 4066.812 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.130464 | 0.12590822 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 4066.81 | 4066.81 | 1.0000 | 0.12590822 | 0.130464 | 14.22 | 8.41 | 0.00619979 | 29962.9 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4066.81 | -18.80 | 0.00088830 | -18.80 | 0.01061882 | 8.1393 | 21.10 | 0.00730623 | 21.10 | 0.00730623 | 37.6541 | 1401.23 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 4066.812 | 4066.812 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.130464 | 0.12590822 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 4066.81 | 4066.81 | 1.0000 | 0.12590822 | 0.130464 | 14.22 | 8.41 | 0.00619979 | 29962.9 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4066.81 | -18.80 | 0.00088830 | -18.80 | 0.01061882 | 8.1393 | 21.10 | 0.00730623 | 21.10 | 0.00730623 | 37.6541 | 1401.23 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC 1SPD DX AC CLG COIL 6KBTU/HR 9.7SEER | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 1805.626 | 1445.684 | 0.109078 | -999.0 | -999.000 | -999.0000 | 1.21778 | 1.00000 | 1020.5692 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.109078 | 0.10526905 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 11:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 11:00:00 | DENVER CENTENNIAL GOLDEN N ANN CLG .4% CONDNS DB=>MWB 1 | 7/21 10:00:00 | 1991.60 | 1991.60 | 0.9066 | 0.10526905 | 0.109078 | 24.44 | 14.21 | 0.00846136 | 46103.2 | 11.60 | 9.59 | 0.00846136 | 32998.7 | -999.0 | -999.00 | -999.00 | -999.00 | 126.667 | 1864.93 | 29.50 | 0.00686230 | 14.59 | 0.01061882 | 9.7351 | 23.89 | 0.00863505 | 23.89 | 0.00864095 | 37.5209 | 1031.44 | 0.00 | 1802.75 | 1301.10 | 0.10110130 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 14.07 | 13.33 | 0.00923349 | 37476.6 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC GAS HTG COIL | Coil:Heating:Fuel | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 3467.531 | 3467.531 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.109078 | 0.10526905 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3467.53 | 3467.53 | 1.0000 | 0.10526905 | 0.109078 | 14.24 | 8.42 | 0.00620239 | 29980.7 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 3467.53 | -18.80 | 0.00088830 | -18.80 | 0.01061882 | 9.7351 | 21.10 | 0.00730723 | 21.10 | 0.00730723 | 37.6592 | 1403.47 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC ELECTRIC BACKUP HTG COIL | Coil:Heating:Electric | AirLoop | AirLoopHVAC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 3467.531 | 3467.531 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 0.9651 | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC FAN | Fan:ConstantVolume | 0.109078 | 0.10526905 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | unknown | unknown | DENVER CENTENNIAL GOLDEN N ANN HTG 99.6% CONDNS DB 1 | 12/21 01:00:00 | 3467.53 | 3467.53 | 1.0000 | 0.10526905 | 0.109078 | 14.24 | 8.42 | 0.00620239 | 29980.7 | 50.00 | 21.21 | 0.00800000 | 70993.1 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 3467.53 | -18.80 | 0.00088830 | -18.80 | 0.01061882 | 9.7351 | 21.10 | 0.00730723 | 21.10 | 0.00730723 | 37.6592 | 1403.47 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 |
Report: System Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| None |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 2 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 5 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 3 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 4 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 1 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 6 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 7 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 8 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | CONTROLLER MECHANICAL VENTILATION 9 | 0.000000 | 0.000508 | 0.000000 | 0.000000 | Sum | 1.00 | 1.00 |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 3.00 | 12.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 3.00 | 12.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 1.00 | 12.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 3.00 | 8.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 3.00 | 10.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 2.00 | 12.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 3.00 | 12.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 2.00 | 12.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 1.00 | 12.00 | 0.00 |
| Facility | 3.00 | 12.00 | 0.00 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.00 | 0.00 | 0.00 | 0.00 |
| Facility | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Average Outdoor Air During Occupied Hours| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 2.77 | 3.11 | 157.51 | 0.395 | 0.224 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 1.12 | 1.26 | 63.71 | 0.394 | 0.448 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 1.12 | 1.26 | 63.71 | 0.394 | 0.447 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 2.72 | 3.06 | 154.58 | 0.395 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 1.10 | 1.24 | 62.53 | 0.395 | 0.224 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 1.10 | 1.24 | 62.53 | 0.395 | 0.224 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 2.77 | 3.11 | 157.51 | 0.395 | 0.224 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 1.12 | 1.26 | 63.71 | 0.394 | 0.448 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 1.12 | 1.26 | 63.71 | 0.394 | 0.447 | 0.000 | 0.000 |
| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 2.77 | 3.11 | 157.51 | 0.000 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 1.12 | 1.26 | 63.71 | 0.000 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 1.12 | 1.26 | 63.71 | 0.000 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 2.72 | 3.06 | 154.58 | 0.000 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 1.10 | 1.24 | 62.53 | 0.000 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 1.10 | 1.24 | 62.53 | 0.000 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 2.77 | 3.11 | 157.51 | 0.000 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 1.12 | 1.26 | 63.71 | 0.000 | 0.000 | 0.000 | 0.000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 1.12 | 1.26 | 63.71 | 0.000 | 0.000 | 0.000 | 0.000 |
Report: Object Count Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Surfaces by Class| Total | Outdoors | |
| Wall | 36 | 12 |
| Floor | 9 | 9 |
| Roof | 9 | 9 |
| Internal Mass | 9 | 0 |
| Building Detached Shading | 0 | 0 |
| Fixed Detached Shading | 0 | 0 |
| Window | 12 | 12 |
| Door | 0 | 0 |
| Glass Door | 0 | 0 |
| Shading | 0 | 0 |
| Overhang | 0 | 0 |
| Fin | 0 | 0 |
| Tubular Daylighting Device Dome | 0 | 0 |
| Tubular Daylighting Device Diffuser | 0 | 0 |
| Count | |
| HVAC Air Loops | 9 |
| Conditioned Zones | 9 |
| Unconditioned Zones | 0 |
| Supply Plenums | 0 |
| Return Plenums | 0 |
| Count | |
| IDF Objects | 0 |
| Defaulted Fields | 0 |
| Fields with Defaults | 0 |
| Autosized Fields | 0 |
| Autosizable Fields | 0 |
| Autocalculated Fields | 0 |
| Autocalculatable Fields | 0 |
Report: Energy Meters
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Annual and Peak Values - Electricity| Electricity Annual Value [GJ] | Electricity Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Electricity Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Electricity:Facility | 0.35 | 1635.00 | 01-JUN-06:00 | 7677.31 | 01-JUN-14:00 |
| Electricity:Building | 0.23 | 918.00 | 01-JUN-23:00 | 4590.00 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.04 | 170.21 | 01-JUN-23:00 | 851.03 | 01-JUN-08:00 |
| InteriorLights:Electricity | 0.13 | 540.00 | 01-JUN-01:00 | 2700.00 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.02 | 100.12 | 01-JUN-01:00 | 500.61 | 01-JUN-08:00 |
| General:InteriorLights:Electricity | 0.13 | 540.00 | 01-JUN-01:00 | 2700.00 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.02 | 68.85 | 01-JUN-23:00 | 344.25 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.01 | 40.50 | 01-JUN-01:00 | 202.50 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.02 | 68.85 | 01-JUN-23:00 | 344.25 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.01 | 40.50 | 01-JUN-01:00 | 202.50 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.04 | 167.04 | 01-JUN-23:00 | 835.22 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.02 | 98.26 | 01-JUN-01:00 | 491.31 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.02 | 67.57 | 01-JUN-23:00 | 337.86 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.01 | 39.75 | 01-JUN-01:00 | 198.74 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.02 | 67.57 | 01-JUN-23:00 | 337.86 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.01 | 39.75 | 01-JUN-01:00 | 198.74 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.04 | 170.21 | 01-JUN-23:00 | 851.03 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.02 | 100.12 | 01-JUN-01:00 | 500.61 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.02 | 68.85 | 01-JUN-23:00 | 344.25 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.01 | 40.50 | 01-JUN-01:00 | 202.50 | 01-JUN-08:00 |
| Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.02 | 68.85 | 01-JUN-23:00 | 344.25 | 01-JUN-08:00 |
| InteriorLights:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.01 | 40.50 | 01-JUN-01:00 | 202.50 | 01-JUN-08:00 |
| InteriorEquipment:Electricity | 0.10 | 378.00 | 01-JUN-18:00 | 1890.00 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.02 | 70.09 | 01-JUN-18:00 | 350.43 | 01-JUN-08:00 |
| General:InteriorEquipment:Electricity | 0.10 | 378.00 | 01-JUN-18:00 | 1890.00 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.01 | 28.35 | 01-JUN-18:00 | 141.75 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.01 | 28.35 | 01-JUN-18:00 | 141.75 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.02 | 68.78 | 01-JUN-18:00 | 343.92 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.01 | 27.82 | 01-JUN-18:00 | 139.12 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.01 | 27.82 | 01-JUN-18:00 | 139.12 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.02 | 70.09 | 01-JUN-18:00 | 350.43 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.01 | 28.35 | 01-JUN-18:00 | 141.75 | 01-JUN-08:00 |
| InteriorEquipment:Electricity:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.01 | 28.35 | 01-JUN-18:00 | 141.75 | 01-JUN-08:00 |
| ElectricityPurchased:Facility | 0.35 | 1635.00 | 01-JUN-06:00 | 7677.31 | 01-JUN-14:00 |
| ElectricityPurchased:Plant | 0.35 | 1635.00 | 01-JUN-06:00 | 7677.31 | 01-JUN-14:00 |
| Cogeneration:ElectricityPurchased | 0.35 | 1635.00 | 01-JUN-06:00 | 7677.31 | 01-JUN-14:00 |
| ElectricitySurplusSold:Facility | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| ElectricitySurplusSold:Plant | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| Cogeneration:ElectricitySurplusSold | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| ElectricityNet:Facility | 0.35 | 1635.00 | 01-JUN-06:00 | 7677.31 | 01-JUN-14:00 |
| ElectricityNet:Plant | 0.35 | 1635.00 | 01-JUN-06:00 | 7677.31 | 01-JUN-14:00 |
| Cogeneration:ElectricityNet | 0.35 | 1635.00 | 01-JUN-06:00 | 7677.31 | 01-JUN-14:00 |
| Electricity:HVAC | 0.08 | 0.00 | 01-JUN-01:00 | 3087.23 | 01-JUN-14:00 |
| Fans:Electricity | 0.06 | 0.00 | 01-JUN-01:00 | 1465.05 | 01-JUN-07:00 |
| General:Fans:Electricity | 0.06 | 0.00 | 01-JUN-01:00 | 1465.05 | 01-JUN-07:00 |
| ExteriorLights:Electricity | 0.04 | 0.00 | 01-JUN-06:00 | 1464.21 | 01-JUN-20:00 |
| Building Facades:ExteriorLights:Electricity | 0.01 | 0.00 | 01-JUN-01:00 | 447.21 | 01-JUN-20:00 |
| Main Entries:ExteriorLights:Electricity | 0.01 | 0.00 | 01-JUN-06:00 | 240.00 | 01-JUN-01:00 |
| Other Doors:ExteriorLights:Electricity | 0.00 | 0.00 | 01-JUN-06:00 | 48.00 | 01-JUN-01:00 |
| Parking Areas and Drives:ExteriorLights:Electricity | 0.03 | 0.00 | 01-JUN-06:00 | 729.00 | 01-JUN-01:00 |
| Cooling:Electricity | 0.02 | 0.00 | 01-JUN-01:00 | 1622.18 | 01-JUN-14:00 |
| Heating:Electricity | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| Electricity:Plant | 0.00 | 0.00 | 01-JUN-01:00 | 0.08 | 01-JUN-08:00 |
| Boiler Parasitic:Heating:Electricity | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| Pumps:Electricity | 0.00 | 0.00 | 01-JUN-01:00 | 0.08 | 01-JUN-08:00 |
| General:Pumps:Electricity | 0.00 | 0.00 | 01-JUN-01:00 | 0.08 | 01-JUN-08:00 |
| Gas Annual Value [GJ] | Gas Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Gas Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Gas:Facility | 0.02 | 0.00 | 01-JUN-01:00 | 794.45 | 01-JUN-17:00 |
| Gas:Plant | 0.02 | 0.00 | 01-JUN-01:00 | 613.86 | 01-JUN-11:00 |
| WaterSystems:Gas | 0.02 | 0.00 | 01-JUN-01:00 | 613.86 | 01-JUN-11:00 |
| General:WaterSystems:Gas | 0.02 | 0.00 | 01-JUN-01:00 | 613.86 | 01-JUN-11:00 |
| Gas:HVAC | 0.00 | 0.00 | 01-JUN-01:00 | 180.58 | 01-JUN-17:00 |
| Heating:Gas | 0.00 | 0.00 | 01-JUN-01:00 | 180.58 | 01-JUN-17:00 |
| General:Heating:Gas | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| Cooling Annual Value [GJ] | Cooling Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Cooling Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| Water:Facility | 0.05 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-12:00 |
| Water:Plant | 0.05 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-12:00 |
| WaterSystems:Water | 0.05 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-12:00 |
| General:WaterSystems:Water | 0.05 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-12:00 |
| MainsWater:Facility | 0.05 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-12:00 |
| MainsWater:Plant | 0.05 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-12:00 |
| WaterSystems:MainsWater | 0.05 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-12:00 |
| General:WaterSystems:MainsWater | 0.05 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-12:00 |
| Annual Value [kg] | Minimum Value [kg/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [kg/s] | Timestamp of Maximum {TIMESTAMP} | |
| Carbon Equivalent:Facility | 0.00 | 0.000 | 01-JUN-01:00 | 0.000 | 01-JUN-01:00 |
| CarbonEquivalentEmissions:Carbon Equivalent | 0.00 | 0.000 | 01-JUN-01:00 | 0.000 | 01-JUN-01:00 |
| Annual Value [m3] | Minimum Value [m3/s] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [m3/s] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [L] | Minimum Value [L] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [L] | Timestamp of Maximum {TIMESTAMP} | |
| None |
| Annual Value [GJ] | Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| PlantLoopHeatingDemand:Facility | 0.00 | 0.00 | 01-JUN-01:00 | 81.95 | 01-JUN-12:00 |
| PlantLoopHeatingDemand:Plant | 0.00 | 0.00 | 01-JUN-01:00 | 81.95 | 01-JUN-12:00 |
| WaterSystems:PlantLoopHeatingDemand | 0.00 | 0.00 | 01-JUN-01:00 | 81.95 | 01-JUN-12:00 |
| General:WaterSystems:PlantLoopHeatingDemand | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| EnergyTransfer:Facility | 0.13 | 0.00 | 01-JUN-01:00 | 9399.69 | 01-JUN-14:00 |
| EnergyTransfer:Building | 0.05 | 0.00 | 01-JUN-01:00 | 3559.09 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.01 | 0.00 | 01-JUN-01:00 | 715.90 | 01-JUN-14:00 |
| Heating:EnergyTransfer | 0.00 | 0.00 | 01-JUN-01:00 | 213.01 | 01-JUN-17:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 4.79 | 01-JUN-07:00 |
| Cooling:EnergyTransfer | 0.05 | 0.00 | 01-JUN-01:00 | 3559.09 | 01-JUN-14:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.01 | 0.00 | 01-JUN-01:00 | 715.90 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 313.21 | 01-JUN-14:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 46.36 | 01-JUN-17:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 313.21 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 261.11 | 01-JUN-14:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 65.07 | 01-JUN-17:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 261.11 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.01 | 0.00 | 01-JUN-01:00 | 656.64 | 01-JUN-14:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.01 | 0.00 | 01-JUN-01:00 | 656.64 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 293.52 | 01-JUN-14:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 16.86 | 01-JUN-07:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 293.52 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 231.15 | 01-JUN-14:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 7.94 | 01-JUN-07:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 231.15 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.01 | 0.00 | 01-JUN-01:00 | 598.48 | 01-JUN-14:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.01 | 0.00 | 01-JUN-01:00 | 598.48 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 269.37 | 01-JUN-14:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 44.39 | 01-JUN-17:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 269.37 | 01-JUN-14:00 |
| EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 219.72 | 01-JUN-14:00 |
| Heating:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 55.59 | 01-JUN-17:00 |
| Cooling:EnergyTransfer:Zone:ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.00 | 0.00 | 01-JUN-01:00 | 219.72 | 01-JUN-14:00 |
| EnergyTransfer:Plant | 0.00 | 0.00 | 01-JUN-01:00 | 80.58 | 01-JUN-12:00 |
| WaterSystems:EnergyTransfer | 0.00 | 0.00 | 01-JUN-01:00 | 80.58 | 01-JUN-12:00 |
| General:WaterSystems:EnergyTransfer | 0.00 | 0.00 | 01-JUN-01:00 | 80.58 | 01-JUN-12:00 |
| EnergyTransfer:HVAC | 0.07 | 0.00 | 01-JUN-01:00 | 5795.46 | 01-JUN-14:00 |
| CoolingCoils:EnergyTransfer | 0.07 | 0.00 | 01-JUN-01:00 | 5795.46 | 01-JUN-14:00 |
| HeatingCoils:EnergyTransfer | 0.00 | 0.00 | 01-JUN-01:00 | 144.47 | 01-JUN-17:00 |
| Boilers:EnergyTransfer | 0.00 | 0.00 | 01-JUN-01:00 | 0.00 | 01-JUN-01:00 |
Report: Sensible Heat Gain Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Annual Building Sensible Heat Gain Components| HVAC Zone Eq & Other Sensible Air Heating [GJ] | HVAC Zone Eq & Other Sensible Air Cooling [GJ] | HVAC Terminal Unit Sensible Air Heating [GJ] | HVAC Terminal Unit Sensible Air Cooling [GJ] | HVAC Input Heated Surface Heating [GJ] | HVAC Input Cooled Surface Cooling [GJ] | People Sensible Heat Addition [GJ] | Lights Sensible Heat Addition [GJ] | Equipment Sensible Heat Addition [GJ] | Window Heat Addition [GJ] | Interzone Air Transfer Heat Addition [GJ] | Infiltration Heat Addition [GJ] | Opaque Surface Conduction and Other Heat Addition [GJ] | Equipment Sensible Heat Removal [GJ] | Window Heat Removal [GJ] | Interzone Air Transfer Heat Removal [GJ] | Infiltration Heat Removal [GJ] | Opaque Surface Conduction and Other Heat Removal [GJ] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.010 | 0.000 | 0.000 | 0.008 | 0.025 | 0.018 | 0.008 | 0.000 | 0.000 | 0.000 | 0.000 | -0.006 | 0.000 | -0.008 | -0.035 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.003 | 0.000 | 0.000 | 0.003 | 0.010 | 0.007 | 0.008 | 0.000 | 0.000 | 0.000 | 0.000 | -0.005 | 0.000 | -0.006 | -0.015 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.003 | 0.000 | 0.000 | 0.003 | 0.010 | 0.007 | 0.006 | 0.000 | 0.000 | 0.000 | 0.000 | -0.005 | 0.000 | -0.006 | -0.014 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.014 | 0.000 | 0.000 | 0.008 | 0.024 | 0.018 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | 0.000 | -0.036 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.004 | 0.000 | 0.000 | 0.003 | 0.010 | 0.007 | 0.005 | 0.000 | 0.000 | 0.000 | 0.000 | -0.002 | 0.000 | -0.003 | -0.016 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.003 | 0.000 | 0.000 | 0.003 | 0.010 | 0.007 | 0.002 | 0.000 | 0.000 | 0.000 | 0.000 | -0.002 | 0.000 | -0.003 | -0.014 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.009 | 0.000 | 0.000 | 0.008 | 0.025 | 0.018 | 0.006 | 0.000 | 0.000 | 0.000 | 0.000 | -0.006 | 0.000 | -0.008 | -0.035 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.003 | 0.000 | 0.000 | 0.003 | 0.010 | 0.007 | 0.007 | 0.000 | 0.000 | 0.000 | 0.000 | -0.004 | 0.000 | -0.006 | -0.015 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 0.000 | 0.000 | 0.000 | -0.002 | 0.000 | 0.000 | 0.003 | 0.010 | 0.007 | 0.005 | 0.000 | 0.000 | 0.000 | 0.000 | -0.004 | 0.000 | -0.006 | -0.014 |
| Total Facility | 0.000 | 0.000 | 0.002 | -0.051 | 0.000 | 0.000 | 0.042 | 0.133 | 0.100 | 0.048 | 0.000 | 0.000 | 0.000 | 0.000 | -0.035 | 0.000 | -0.045 | -0.194 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -715.64 | 0.00 | 0.00 | 218.26 | 500.61 | 350.43 | 570.22 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -65.25 | -858.61 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -313.13 | 0.00 | 0.00 | 88.43 | 202.50 | 141.75 | 490.04 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -52.69 | -556.90 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -261.05 | 0.00 | 0.00 | 88.69 | 202.50 | 141.75 | 415.37 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -52.54 | -534.72 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -656.32 | 0.00 | 0.00 | 214.16 | 491.31 | 343.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | 0.00 | -393.06 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -293.43 | 0.00 | 0.00 | 86.64 | 198.74 | 139.12 | 254.29 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -25.91 | -359.45 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -231.09 | 0.00 | 0.00 | 86.67 | 198.74 | 139.12 | 180.04 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -25.90 | -347.57 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -598.27 | 0.00 | 0.00 | 218.26 | 500.61 | 350.43 | 452.09 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -65.25 | -857.87 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -269.30 | 0.00 | 0.00 | 88.51 | 202.50 | 141.75 | 443.79 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -52.63 | -554.62 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -219.67 | 0.00 | 0.00 | 88.75 | 202.50 | 141.75 | 368.93 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -52.49 | -529.76 |
| Total Facility | 01-JUN-14:00 | 0.00 | 0.00 | 0.00 | -3557.90 | 0.00 | 0.00 | 1178.38 | 2700.00 | 1890.00 | 3174.76 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -392.67 | -4992.57 |
| Time of Peak {TIMESTAMP} | HVAC Zone Eq & Other Sensible Air Heating [W] | HVAC Zone Eq & Other Sensible Air Cooling [W] | HVAC Terminal Unit Sensible Air Heating [W] | HVAC Terminal Unit Sensible Air Cooling [W] | HVAC Input Heated Surface Heating [W] | HVAC Input Cooled Surface Cooling [W] | People Sensible Heat Addition [W] | Lights Sensible Heat Addition [W] | Equipment Sensible Heat Addition [W] | Window Heat Addition [W] | Interzone Air Transfer Heat Addition [W] | Infiltration Heat Addition [W] | Opaque Surface Conduction and Other Heat Addition [W] | Equipment Sensible Heat Removal [W] | Window Heat Removal [W] | Interzone Air Transfer Heat Removal [W] | Infiltration Heat Removal [W] | Opaque Surface Conduction and Other Heat Removal [W] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 01-JUN-07:00 | 0.00 | 0.00 | 9.58 | -0.00 | 0.00 | 0.00 | 51.47 | 233.62 | 175.21 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -20.45 | 0.00 | -63.72 | -385.72 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 01-JUN-16:40 | 0.00 | 0.00 | 59.52 | -0.00 | 0.00 | 0.00 | 28.25 | 137.25 | 70.87 | 320.55 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -218.74 | -397.70 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 01-JUN-16:40 | 0.00 | 0.00 | 88.16 | -0.00 | 0.00 | 0.00 | 28.25 | 137.25 | 70.87 | 51.69 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -211.18 | -165.04 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 01-JUN-06:30 | 0.00 | 0.00 | 19.22 | -0.00 | 0.00 | 0.00 | 20.38 | 92.74 | 69.56 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -7.50 | 0.00 | -25.59 | -168.81 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 01-JUN-06:30 | 0.00 | 0.00 | 9.34 | -0.00 | 0.00 | 0.00 | 20.68 | 92.74 | 69.56 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -6.11 | 0.00 | -24.72 | -161.49 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | - | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 01-JUN-16:40 | 0.00 | 0.00 | 56.71 | -0.00 | 0.00 | 0.00 | 28.25 | 137.25 | 70.87 | 329.61 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -217.61 | -405.09 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 01-JUN-16:40 | 0.00 | 0.00 | 80.10 | -0.00 | 0.00 | 0.00 | 28.25 | 137.25 | 70.87 | 60.67 | 0.00 | 0.00 | 0.00 | 0.00 | -0.00 | 0.00 | -209.14 | -168.01 |
| Total Facility | 01-JUN-16:40 | -358.30 | 358.30 | 289.31 | -358.30 | 0.00 | 0.00 | 376.63 | 1830.00 | 945.00 | 1216.92 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | -1608.24 | -2691.31 |
Report: Standard 62.1 Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
System Ventilation Requirements for Cooling| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow - Vot [m3/s] | Percent Outdoor Air - %OA | Environment Name of Peak System Population - Ps | Date and Time of Last Peak System Population - Ps | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 0.2211 | 0.0000 | 3.1149 | 1.0000 | 0.0263 | 0.2211 | 1.0000 | 1.0000 | 0.0263 | 0.1187 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 0.1384 | 0.0000 | 1.2600 | 1.0000 | 0.0106 | 0.1384 | 1.0000 | 1.0000 | 0.0106 | 0.0767 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 0.1203 | 0.0000 | 1.2600 | 1.0000 | 0.0106 | 0.1203 | 1.0000 | 1.0000 | 0.0106 | 0.0883 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 0.1453 | 0.0000 | 3.0570 | 1.0000 | 0.0258 | 0.1453 | 1.0000 | 1.0000 | 0.0258 | 0.1773 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 0.1169 | 0.0000 | 1.2366 | 1.0000 | 0.0104 | 0.1169 | 1.0000 | 1.0000 | 0.0104 | 0.0891 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 0.0994 | 0.0000 | 1.2366 | 1.0000 | 0.0104 | 0.0994 | 1.0000 | 1.0000 | 0.0104 | 0.1049 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 0.1807 | 0.0000 | 3.1149 | 1.0000 | 0.0263 | 0.1807 | 1.0000 | 1.0000 | 0.0263 | 0.1453 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 0.1305 | 0.0000 | 1.2600 | 1.0000 | 0.0106 | 0.1305 | 1.0000 | 1.0000 | 0.0106 | 0.0814 | ||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 0.1091 | 0.0000 | 1.2600 | 1.0000 | 0.0106 | 0.1091 | 1.0000 | 1.0000 | 0.0106 | 0.0974 |
| Sum of Zone Primary Air Flow - Vpz-sum [m3/s] | System Population - Ps | Sum of Zone Population - Pz-sum | Occupant Diversity - D | Uncorrected Outdoor Air Intake Airflow - Vou [m3/s] | System Primary Airflow - Vps [m3/s] | Average Outdoor Air Fraction - Xs | System Ventilation Efficiency - Ev | Outdoor Air Intake Flow Vot [m3/s] | Percent Outdoor Air - %OA | Environment Name of Peak System Population - Ps | Date and Time of Last Peak System Population - Ps | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 3.1149 | 1.0000 | 0.0263 | 0.0000 | 0.2771 | 1.0000 | 0.0263 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 1.2600 | 1.0000 | 0.0106 | 0.0000 | 0.1723 | 1.0000 | 0.0106 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 1.2600 | 1.0000 | 0.0106 | 0.0000 | 0.1720 | 1.0000 | 0.0106 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 3.0570 | 1.0000 | 0.0258 | 0.0000 | 0.6095 | 1.0000 | 0.0258 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 1.2366 | 1.0000 | 0.0104 | 0.0000 | 0.2640 | 1.0000 | 0.0104 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 1.2366 | 1.0000 | 0.0104 | 0.0000 | 0.2633 | 1.0000 | 0.0104 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 3.1149 | 1.0000 | 0.0263 | 0.0000 | 0.2786 | 1.0000 | 0.0263 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 1.2600 | 1.0000 | 0.0106 | 0.0000 | 0.1724 | 1.0000 | 0.0106 | |||
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 1.2600 | 1.0000 | 0.0106 | 0.0000 | 0.1721 | 1.0000 | 0.0106 |
| AirLoop Name | People Outdoor Air Rate - Rp [m3/s-person] | Zone Population - Pz | Area Outdoor Air Rate - Ra [m3/s-m2] | Zone Floor Area - Az [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Air Distribution Effectiveness - Ez-clg | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Air Distribution Effectiveness - Ez-htg | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 0.000000 | 3.1149 | 0.000508 | 51.68 | 0.0263 | 1.0000 | 0.0263 | 1.000 | 0.0263 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 0.000000 | 1.2600 | 0.000508 | 20.90 | 0.0106 | 1.0000 | 0.0106 | 1.000 | 0.0106 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 0.000000 | 1.2600 | 0.000508 | 20.90 | 0.0106 | 1.0000 | 0.0106 | 1.000 | 0.0106 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 0.000000 | 3.0570 | 0.000508 | 50.72 | 0.0258 | 1.0000 | 0.0258 | 1.000 | 0.0258 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 0.000000 | 1.2366 | 0.000508 | 20.51 | 0.0104 | 1.0000 | 0.0104 | 1.000 | 0.0104 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 0.000000 | 1.2366 | 0.000508 | 20.51 | 0.0104 | 1.0000 | 0.0104 | 1.000 | 0.0104 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 0.000000 | 3.1149 | 0.000508 | 51.68 | 0.0263 | 1.0000 | 0.0263 | 1.000 | 0.0263 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 0.000000 | 1.2600 | 0.000508 | 20.90 | 0.0106 | 1.0000 | 0.0106 | 1.000 | 0.0106 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 0.000000 | 1.2600 | 0.000508 | 20.90 | 0.0106 | 1.0000 | 0.0106 | 1.000 | 0.0106 |
| People Outdoor Air Rate - Rp [m3/s-person] | Sum of Zone Population - Pz-sum | Area Outdoor Air Rate - Ra [m3/s-m2] | Sum of Zone Floor Area - Az-sum [m2] | Breathing Zone Outdoor Airflow - Vbz [m3/s] | Cooling Zone Outdoor Airflow - Voz-clg [m3/s] | Heating Zone Outdoor Airflow - Voz-htg [m3/s] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 0.000000 | 3.11 | 0.000508 | 51.6755 | 0.0263 | 0.0263 | 0.0263 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 0.000000 | 1.26 | 0.000508 | 20.9032 | 0.0106 | 0.0106 | 0.0106 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 0.000000 | 1.26 | 0.000508 | 20.9032 | 0.0106 | 0.0106 | 0.0106 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 0.000000 | 3.06 | 0.000508 | 50.7156 | 0.0258 | 0.0258 | 0.0258 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 0.000000 | 1.24 | 0.000508 | 20.5149 | 0.0104 | 0.0104 | 0.0104 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 0.000000 | 1.24 | 0.000508 | 20.5149 | 0.0104 | 0.0104 | 0.0104 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 0.000000 | 3.11 | 0.000508 | 51.6755 | 0.0263 | 0.0263 | 0.0263 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 0.000000 | 1.26 | 0.000508 | 20.9032 | 0.0106 | 0.0106 | 0.0106 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 0.000000 | 1.26 | 0.000508 | 20.9032 | 0.0106 | 0.0106 | 0.0106 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.2211 | 0.2211 | 0.0000 | 0.0263 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.1384 | 0.1384 | 0.0000 | 0.0106 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.1203 | 0.1203 | 0.0000 | 0.0106 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.1453 | 0.1453 | 0.0000 | 0.0258 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.1169 | 0.1169 | 0.0000 | 0.0104 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0994 | 0.0994 | 0.0000 | 0.0104 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.1807 | 0.1807 | 0.0000 | 0.0263 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.1305 | 0.1305 | 0.0000 | 0.0106 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.1091 | 0.1091 | 0.0000 | 0.0106 | 0.0000 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Cooling - Voz-clg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 0.2211 | 0.2211 | 0.2211 | 0.0000 | 0.0263 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 0.1384 | 0.1384 | 0.1384 | 0.0000 | 0.0106 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 0.1203 | 0.1203 | 0.1203 | 0.0000 | 0.0106 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 0.1453 | 0.1453 | 0.1453 | 0.0000 | 0.0258 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 0.1169 | 0.1169 | 0.1169 | 0.0000 | 0.0104 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 0.0994 | 0.0994 | 0.0994 | 0.0000 | 0.0104 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 0.1807 | 0.1807 | 0.1807 | 0.0000 | 0.0263 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 0.1305 | 0.1305 | 0.1305 | 0.0000 | 0.0106 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 0.1091 | 0.1091 | 0.1091 | 0.0000 | 0.0106 | 1.0000 |
| AirLoop Name | Box Type | Zone Primary Airflow - Vpz [m3/s] | Zone Discharge Airflow - Vdz [m3/s] | Minimum Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Primary Outdoor Air Fraction - Zpz | Primary Air Fraction - Ep | Secondary Recirculation Fraction- Er | Supply Air Fraction- Fa | Mixed Air Fraction - Fb | Outdoor Air Fraction - Fc | Zone Ventilation Efficiency - Evz | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0263 | 0.2771 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0106 | 0.1723 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0106 | 0.1720 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0258 | 0.6095 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0104 | 0.2640 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0104 | 0.2633 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0263 | 0.2786 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0106 | 0.1724 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | AIRTERMINAL:SINGLEDUCT:CONSTANTVOLUME:NOREHEAT | 0.0000 | 0.0000 | 0.0000 | 0.0106 | 0.1721 | 1.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 1.0000 |
| Sum of Zone Primary Airflow - Vpz-sum [m3/s] | System Primary Airflow - Vps [m3/s] | Sum of Zone Discharge Airflow - Vdz-sum [m3/s] | Sum of Min Zone Primary Airflow - Vpz-min [m3/s] | Zone Outdoor Airflow Heating - Voz-htg [m3/s] | Zone Ventilation Efficiency - Evz-min | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0263 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0106 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0106 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0258 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0104 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0104 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0263 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0106 | 1.0000 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND PSZ-AC | 0.0000 | 0.0000 | 0.0000 | 0.0000 | 0.0106 | 1.0000 |
Report: LEED Summary
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Sec1.1A-General Information| Data | |
| Weather File | RUN PERIOD 1 ** Denver Centennial Golden Nr CO USA TMY3 WMO#=724666 |
| Total gross floor area [m2] | 278.71 |
| Principal Heating Source | Natural Gas |
| Space Area [m2] | Regularly Occupied Area [m2] | Unconditioned Area [m2] | Typical Hours/Week in Operation [hr/wk] | |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A - STORY GROUND | 51.68 | 51.68 | 0.00 | 119.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_A - STORY GROUND | 20.90 | 20.90 | 0.00 | 119.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE A END_B - STORY GROUND | 20.90 | 20.90 | 0.00 | 119.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B - STORY GROUND | 50.72 | 50.72 | 0.00 | 119.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_A - STORY GROUND | 20.51 | 20.51 | 0.00 | 119.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE B END_B - STORY GROUND | 20.51 | 20.51 | 0.00 | 119.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C - STORY GROUND | 51.68 | 51.68 | 0.00 | 119.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_A - STORY GROUND | 20.90 | 20.90 | 0.00 | 119.00 |
| ZONE OFFICE WHOLEBUILDING - SM OFFICE C END_B - STORY GROUND | 20.90 | 20.90 | 0.00 | 119.00 |
| Totals | 278.71 | 278.71 | 0.00 |
| Data | |
| Number of hours heating loads not met | 0.00 |
| Number of hours cooling loads not met | 0.00 |
| Number of hours not met | 0.00 |
| Utility Rate | Virtual Rate [$/unit energy] | Units of Energy | Units of Demand | |
| Electricity | ELECTRICITY TARIFF | 15.283 | kWh | kW |
| Natural Gas | GAS TARIFF | 3296.248 | Therm | Therm/Day |
| Other | WATER TARIFF | 1.321 | /Hr |
| Electric Energy Use [GJ] | Electric Demand [W] | Natural Gas Energy Use [GJ] | Natural Gas Demand [W] | Additional Fuel Use [GJ] | Additional Fuel Demand [W] | District Cooling Use [GJ] | District Cooling Demand [W] | District Heating Use [GJ] | District Heating Demand [W] | |
| Heating -- General | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heating -- Boiler Parasitic | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Cooling -- Not Subdivided | 0.02 | 1622.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Lighting -- General | 0.13 | 2700.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting -- Building Facades | 0.01 | 447.21 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting -- Main Entries | 0.01 | 240.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting -- Other Doors | 0.00 | 48.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Lighting -- Parking Areas and Drives | 0.03 | 729.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Interior Equipment -- General | 0.10 | 1890.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Exterior Equipment -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Fans -- General | 0.06 | 1465.05 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Pumps -- General | 0.00 | 0.08 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Rejection -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Humidification -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Heat Recovery -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Water Systems -- General | 0.00 | 0.00 | 0.02 | 613.86 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Refrigeration -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Generators -- Not Subdivided | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Process Subtotal [GJ] | Total Energy Use [GJ] | |
| Electricity | 0.10 | 0.35 |
| Natural Gas | 0.00 | 0.02 |
| Total | 0.10 | 0.37 |
| Additional | 0.00 | 0.00 |
| Process Subtotal [$] | Total Energy Cost [$] | |
| Electricity | 422.92 | 1500.88 |
| Natural Gas | 0.00 | 600.09 |
| Other | 0.06 | |
| Total | 422.92 | 2101.04 |
| Additional | 0.00 |
| Rated Capacity [kW] | Annual Energy Generated [GJ] | |
| Photovoltaic | 0.00 | 0.00 |
| Wind | 0.00 | 0.00 |
| Electricty [MJ/m2] | |
| Interior Lighting (All) | 0.48 |
| Space Heating | 0.00 |
| Space Cooling | 0.07 |
| Fans (All) | 0.21 |
| Service Water Heating | 0.00 |
| Receptacle Equipment | 0.36 |
| Miscellaneous (All) | 1.27 |
| Subtotal | 1.27 |
| Natural Gas [MJ/m2] | |
| Space Heating | 0.00 |
| Service Water Heating | 0.06 |
| Miscellaneous (All) | 0.07 |
| Subtotal | 0.07 |
| Additional [MJ/m2] | |
| Subtotal | 0.00 |
| Miscellaneous | 0.00 |
| Percent [%] | |
| Interior Lighting (All) | 35.58 |
| Space Heating | 0.32 |
| Space Cooling | 5.42 |
| Fans (All) | 15.57 |
| Service Water Heating | 4.83 |
| Receptacle Equipment | 26.73 |
| Miscellaneous | 11.55 |
| Equivalent Full Load Hours of Operation Per Year [hr] | Hours > 1% [hr] | |
| None |
| First Object Used | Month Assumed | 11am First Wednesday [C] | Days with Same 11am Value | 11pm First Wednesday [C] | Days with Same 11pm Value | |
| OFFICESMALL HTGSETP_SCH_NO_OPTIMUM | OFFICE WHOLEBUILDING - SM OFFICE - 90.1-2004 THERMOSTAT 4 | January | 21.11 | 365 | 15.56 | 365 |
| OFFICESMALL CLGSETP_SCH_NO_OPTIMUM | OFFICE WHOLEBUILDING - SM OFFICE - 90.1-2004 THERMOSTAT 4 | July | 23.89 | 365 | 29.44 | 365 |
Report: BUILDING ENERGY PERFORMANCE - ELECTRICITY
For: Meter
Timestamp: 2020-03-22 22:58:43
Custom Monthly Report| INTERIORLIGHTS:ELECTRICITY [J] | EXTERIORLIGHTS:ELECTRICITY [J] | INTERIOREQUIPMENT:ELECTRICITY [J] | EXTERIOREQUIPMENT:ELECTRICITY [] | FANS:ELECTRICITY [J] | PUMPS:ELECTRICITY [J] | HEATING:ELECTRICITY [J] | COOLING:ELECTRICITY [J] | HEATREJECTION:ELECTRICITY [] | HUMIDIFIER:ELECTRICITY [] | HEATRECOVERY:ELECTRICITY [] | WATERSYSTEMS:ELECTRICITY [] | COGENERATION:ELECTRICITY [] | REFRIGERATION:ELECTRICITY [] | |
| January | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| February | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| March | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| April | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| May | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| June | 0.132624E+09 | 43051875.78 | 99610560.00 | 0.00 | 58015801.02 | 4314.33 | 0.00 | 20200462.31 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| July | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| August | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| September | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| October | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| November | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| December | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| Annual Sum or Average | 0.132624E+09 | 43051875.78 | 99610560.00 | 58015801.02 | 4314.33 | 0.00 | 20200462.31 | |||||||
| Minimum of Months | 0.132624E+09 | 43051875.78 | 99610560.00 | 0.00 | 58015801.02 | 4314.33 | 0.00 | 20200462.31 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Maximum of Months | 0.132624E+09 | 43051875.78 | 99610560.00 | 0.00 | 58015801.02 | 4314.33 | 0.00 | 20200462.31 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: BUILDING ENERGY PERFORMANCE - NATURAL GAS
For: Meter
Timestamp: 2020-03-22 22:58:43
Custom Monthly Report| INTERIOREQUIPMENT:GAS [] | EXTERIOREQUIPMENT:GAS [] | HEATING:GAS [J] | COOLING:GAS [] | WATERSYSTEMS:GAS [J] | COGENERATION:GAS [] | |
| January | - | - | - | - | - | - |
| February | - | - | - | - | - | - |
| March | - | - | - | - | - | - |
| April | - | - | - | - | - | - |
| May | - | - | - | - | - | - |
| June | 0.00 | 0.00 | 1192009.42 | 0.00 | 18015572.73 | 0.00 |
| July | - | - | - | - | - | - |
| August | - | - | - | - | - | - |
| September | - | - | - | - | - | - |
| October | - | - | - | - | - | - |
| November | - | - | - | - | - | - |
| December | - | - | - | - | - | - |
| Annual Sum or Average | 1192009.42 | 18015572.73 | ||||
| Minimum of Months | 0.00 | 0.00 | 1192009.42 | 0.00 | 18015572.73 | 0.00 |
| Maximum of Months | 0.00 | 0.00 | 1192009.42 | 0.00 | 18015572.73 | 0.00 |
Report: BUILDING ENERGY PERFORMANCE - ELECTRICITY PEAK DEMAND
For: Meter
Timestamp: 2020-03-22 22:58:43
Custom Monthly Report| ELECTRICITY:FACILITY {Maximum}[W] | ELECTRICITY:FACILITY {TIMESTAMP} | INTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | EXTERIORLIGHTS:ELECTRICITY {AT MAX/MIN} [W] | INTERIOREQUIPMENT:ELECTRICITY {AT MAX/MIN} [W] | EXTERIOREQUIPMENT:ELECTRICITY [] | FANS:ELECTRICITY {AT MAX/MIN} [W] | PUMPS:ELECTRICITY {AT MAX/MIN} [W] | HEATING:ELECTRICITY {AT MAX/MIN} [W] | COOLING:ELECTRICITY {AT MAX/MIN} [W] | HEATREJECTION:ELECTRICITY [] | HUMIDIFIER:ELECTRICITY [] | HEATRECOVERY:ELECTRICITY [] | WATERSYSTEMS:ELECTRICITY [] | COGENERATION:ELECTRICITY [] | |
| January | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| February | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| March | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| April | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| May | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| June | 7677.31 | 01-JUN-13:00 | 2700.00 | 0.00 | 1890.00 | 0.00 | 1465.05 | 0.08 | 0.00 | 1622.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| July | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| August | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| September | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| October | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| November | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| December | - | - | - | - | - | - | - | - | - | - | - | - | - | - | - |
| Annual Sum or Average | |||||||||||||||
| Minimum of Months | 7677.31 | 2700.00 | 0.00 | 1890.00 | 0.00 | 1465.05 | 0.08 | 0.00 | 1622.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | |
| Maximum of Months | 7677.31 | 2700.00 | 0.00 | 1890.00 | 0.00 | 1465.05 | 0.08 | 0.00 | 1622.18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: BUILDING ENERGY PERFORMANCE - NATURAL GAS PEAK DEMAND
For: Meter
Timestamp: 2020-03-22 22:58:43
Custom Monthly Report| GAS:FACILITY {Maximum}[W] | GAS:FACILITY {TIMESTAMP} | INTERIOREQUIPMENT:GAS [] | EXTERIOREQUIPMENT:GAS [] | HEATING:GAS {AT MAX/MIN} [W] | COOLING:GAS [] | WATERSYSTEMS:GAS {AT MAX/MIN} [W] | COGENERATION:GAS [] | |
| January | - | - | - | - | - | - | - | - |
| February | - | - | - | - | - | - | - | - |
| March | - | - | - | - | - | - | - | - |
| April | - | - | - | - | - | - | - | - |
| May | - | - | - | - | - | - | - | - |
| June | 794.45 | 01-JUN-16:00 | 0.00 | 0.00 | 180.58 | 0.00 | 613.86 | 0.00 |
| July | - | - | - | - | - | - | - | - |
| August | - | - | - | - | - | - | - | - |
| September | - | - | - | - | - | - | - | - |
| October | - | - | - | - | - | - | - | - |
| November | - | - | - | - | - | - | - | - |
| December | - | - | - | - | - | - | - | - |
| Annual Sum or Average | ||||||||
| Minimum of Months | 794.45 | 0.00 | 0.00 | 180.58 | 0.00 | 613.86 | 0.00 | |
| Maximum of Months | 794.45 | 0.00 | 0.00 | 180.58 | 0.00 | 613.86 | 0.00 |
Report: Economics Results Summary Report
For: Entire Facility
Timestamp: 2020-03-22 22:58:43
Annual Cost| Electric | Gas | Other | Total | |
| Cost [$] | 1500.88 | 600.09 | 0.06 | 2101.04 |
| Cost per Total Building Area [$/m2] | 5.39 | 2.15 | 0.00 | 7.54 |
| Cost per Net Conditioned Building Area [$/m2] | 5.39 | 2.15 | 0.00 | 7.54 |
| Selected | Qualified | Meter | Buy or Sell | Group | Annual Cost ($) | |
| ELECTRICITY TARIFF | Yes | Yes | ELECTRICITYPURCHASED:FACILITY | Buy | (none) | 1500.88 |
| GAS TARIFF | Yes | Yes | GAS:FACILITY | Buy | (none) | 600.09 |
| WATER TARIFF | Yes | Yes | WATER:FACILITY | Buy | (none) | 0.06 |
| DISTRICTHEATING TARIFF | Yes | Yes | DISTRICTHEATING:FACILITY | Buy | (none) | 0.00 |
| DISTRICTCOOLING TARIFF | No | Yes | DISTRICTCOOLING:FACILITY | Buy | (none) | 0.00 |
Report: Tariff Report
For: ELECTRICITY TARIFF
Timestamp: 2020-03-22 22:58:43
General| Parameter | |
| Meter | ELECTRICITYPURCHASED:FACILITY |
| Selected | Yes |
| Group | (none) |
| Qualified | Yes |
| Disqualifier | n/a |
| Computation | automatic |
| Units | kWh |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| EnergyCharges ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 11.78 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 11.78 | 11.78 |
| DemandCharges ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 49.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 49.10 | 49.10 |
| ServiceCharges ($) | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 1440.00 | 120.00 |
| Basis ($) | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 180.88 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 1500.88 | 180.88 |
| Adjustment ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Surcharge ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subtotal ($) | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 180.88 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 1500.88 | 180.88 |
| Taxes ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total ($) | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 180.88 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 120.00 | 1500.88 | 180.88 |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | Category | |
| ELECTRICITYTARIFFENERGYCHARGE ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 11.78 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 11.78 | 11.78 | EnergyCharges |
| ELECTRICITYTARIFFDEMANDCHARGE ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 49.10 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 49.10 | 49.10 | DemandCharges |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| TotalEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 98.20 |
| TotalDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| TotalEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 98.20 |
| TotalDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| PeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 98.20 |
| PeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| ShoulderEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ShoulderDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| OffPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| OffPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MidPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MidPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakExceedsOffPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| OffPeakExceedsPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakExceedsMidPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| MidPeakExceedsPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakExceedsShoulder | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| ShoulderExceedsPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| IsWinter | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 1.00 | 1.00 |
| IsNotWinter | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 11.00 | 1.00 |
| IsSpring | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| IsNotSpring | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 12.00 | 1.00 |
| IsSummer | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| IsNotSummer | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 12.00 | 1.00 |
| IsAutumn | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| IsNotAutumn | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 12.00 | 1.00 |
| PeakAndShoulderEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 98.20 |
| PeakAndShoulderDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| PeakAndMidPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 98.20 |
| PeakAndMidPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| ShoulderAndOffPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ShoulderAndOffPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakAndOffPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 98.20 | 98.20 |
| PeakAndOffPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 4.09 | 4.09 |
| RealTimePriceCosts | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| AboveCustomerBaseCosts | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| BelowCustomerBaseCosts | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| AboveCustomerBaseEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| BelowCustomerBaseEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| NotIncluded | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Tariff Report
For: GAS TARIFF
Timestamp: 2020-03-22 22:58:43
General| Parameter | |
| Meter | GAS:FACILITY |
| Selected | Yes |
| Group | (none) |
| Qualified | Yes |
| Disqualifier | n/a |
| Computation | automatic |
| Units | Therm |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| EnergyCharges ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0910 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.09 | 0.09 |
| DemandCharges ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ServiceCharges ($) | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 600.00 | 50.00 |
| Basis ($) | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.09 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 600.09 | 50.09 |
| Adjustment ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Surcharge ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subtotal ($) | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.09 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 600.09 | 50.09 |
| Taxes ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total ($) | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.09 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 50.00 | 600.09 | 50.09 |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | Category | |
| GASTARIFFENERGYCHARGE ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0910 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.09 | 0.09 | EnergyCharges |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| TotalEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.1821 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.18 | 0.18 |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| TotalEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.1821 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.18 | 0.18 |
| TotalDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0076 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.01 | 0.01 |
| PeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.1821 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.18 | 0.18 |
| PeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0076 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.01 | 0.01 |
| ShoulderEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ShoulderDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| OffPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| OffPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MidPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MidPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakExceedsOffPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0076 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.01 | 0.01 |
| OffPeakExceedsPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakExceedsMidPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0076 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.01 | 0.01 |
| MidPeakExceedsPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakExceedsShoulder | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0076 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.01 | 0.01 |
| ShoulderExceedsPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| IsWinter | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 1.00 | 1.00 |
| IsNotWinter | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 11.00 | 1.00 |
| IsSpring | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| IsNotSpring | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 12.00 | 1.00 |
| IsSummer | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| IsNotSummer | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 12.00 | 1.00 |
| IsAutumn | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| IsNotAutumn | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 1.00 | 12.00 | 1.00 |
| PeakAndShoulderEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.1821 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.18 | 0.18 |
| PeakAndShoulderDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0076 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.01 | 0.01 |
| PeakAndMidPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.1821 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.18 | 0.18 |
| PeakAndMidPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0076 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.01 | 0.01 |
| ShoulderAndOffPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ShoulderAndOffPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakAndOffPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.1821 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.18 | 0.18 |
| PeakAndOffPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0076 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.01 | 0.01 |
| RealTimePriceCosts | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| AboveCustomerBaseCosts | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| BelowCustomerBaseCosts | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| AboveCustomerBaseEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| BelowCustomerBaseEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| NotIncluded | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
Report: Tariff Report
For: WATER TARIFF
Timestamp: 2020-03-22 22:58:43
General| Parameter | |
| Meter | WATER:FACILITY |
| Selected | Yes |
| Group | (none) |
| Qualified | Yes |
| Disqualifier | n/a |
| Computation | automatic |
| Units | User Defined |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| EnergyCharges ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0649 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 | 0.06 |
| DemandCharges ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ServiceCharges ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Basis ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0649 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 | 0.06 |
| Adjustment ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Surcharge ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Subtotal ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0649 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 | 0.06 |
| Taxes ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Total ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0649 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 | 0.06 |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | Category | |
| WATERTARIFFENERGYCHARGE ($) | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0649 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.06 | 0.06 | EnergyCharges |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| TotalEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0492 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.05 | 0.05 |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max |
| Jan | Feb | Mar | Apr | May | Jun | Jul | Aug | Sep | Oct | Nov | Dec | Sum | Max | |
| TotalEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0492 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.05 | 0.05 |
| TotalDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.0492 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.05 | 0.05 |
| PeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ShoulderEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| ShoulderDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| OffPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| OffPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MidPeakEnergy | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MidPeakDemand | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakExceedsOffPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| OffPeakExceedsPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| PeakExceedsMidPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| MidPeakExceedsPeak | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |