| 3 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 13 | 11615.4 | 6391.4 | 6.54 | 4 |
| 4 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 14 | 10089.0 | 5551.5 | 6.54 | 4 |
| 5 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 4 | 8323.9 | 4580.3 | 6.54 | 4 |
| 6 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 5 | 6590.3 | 3626.4 | 6.54 | 4 |
| 7 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 6 | 4940.1 | 2718.3 | 6.54 | 4 |
| 8 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 7 | 8323.9 | 4580.3 | 6.54 | 4 |
| 9 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 8 | 9539.0 | 5248.9 | 6.54 | 4 |
| 10 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 9 | 10867.0 | 5979.6 | 6.54 | 4 |
| 11 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 10 | 9514.9 | 5235.6 | 6.54 | 4 |
| 12 | Coil:Heating:DX:SingleSpeed | 1 SPD DX HTG COIL 11 | 8323.9 | 4580.3 | 6.54 | 4 |
| Environment Name | Environment Type | Start Date | End Date | Start DayOfWeek | Duration {#days} | Source:Start DayOfWeek | Use Daylight Saving | Use Holidays | Apply Weekend Holiday Rule | Use Rain Values | Use Snow Values | |
| 1 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | SizingPeriod:DesignDay | 07/21 | 07/21 | SummerDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 2 | ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | SizingPeriod:DesignDay | 07/21 | 07/21 | SummerDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 3 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | SizingPeriod:DesignDay | 07/21 | 07/21 | SummerDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 4 | ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | SizingPeriod:DesignDay | 07/21 | 07/21 | SummerDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 5 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | SizingPeriod:DesignDay | 01/21 | 01/21 | WinterDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 6 | ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | SizingPeriod:DesignDay | 01/21 | 01/21 | WinterDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 7 | ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | SizingPeriod:DesignDay | 01/21 | 01/21 | WinterDesignDay | 1 | N/A | N/A | N/A | N/A | N/A | N/A |
| 8 | RUN PERIOD 1 | WeatherFileRunPeriod | 01/01 | 12/31 | Sunday | 365 | Use RunPeriod Specified Day | No | No | No | Yes | Yes |
| Daylight Saving Indicator | Source | Start Date | End Date | |
| 1 | No | SizingPeriod:DesignDay | ||
| 2 | No | SizingPeriod:DesignDay | ||
| 3 | No | SizingPeriod:DesignDay | ||
| 4 | No | SizingPeriod:DesignDay | ||
| 5 | No | SizingPeriod:DesignDay | ||
| 6 | No | SizingPeriod:DesignDay | ||
| 7 | No | SizingPeriod:DesignDay | ||
| 8 | No | RunPeriod Object |
| NumberofWarmupDays | |
| 1 | 6 |
| 2 | 6 |
| 3 | 6 |
| 4 | 6 |
| 5 | 6 |
| 6 | 6 |
| 7 | 6 |
| 8 | 6 |
| Max Dry-Bulb Temp {C} | Temp Range {dC} | Temp Range Ind Type | Hum Ind Value at Max Temp | Hum Ind Type | Pressure {Pa} | Wind Direction {deg CW from N} | Wind Speed {m/s} | Clearness | Rain | Snow | |
| 1 | 23.20 | 7.50 | DefaultMultipliers | 100618 | 260 | 3.8 | 0.00 | No | No | ||
| 2 | 16.40 | 7.50 | DefaultMultipliers | 100618 | 260 | 3.8 | 0.00 | No | No | ||
| 3 | 21.30 | 7.50 | DefaultMultipliers | 100618 | 260 | 3.8 | 0.00 | No | No | ||
| 4 | 21.20 | 7.50 | DefaultMultipliers | 100618 | 260 | 3.8 | 0.00 | No | No | ||
| 5 | -26.00 | 0.00 | DefaultMultipliers | 100618 | 50 | 2.2 | 0.00 | No | No | ||
| 6 | -3.10 | 0.00 | DefaultMultipliers | 100618 | 50 | 10.2 | 0.00 | No | No | ||
| 7 | -23.70 | 0.00 | DefaultMultipliers | 100618 | 50 | 2.2 | 0.00 | No | No |
| DayOfYear | ASHRAE A Coeff | ASHRAE B Coeff | ASHRAE C Coeff | Solar Constant-Annual Variation | Eq of Time {minutes} | Solar Declination Angle {deg} | Solar Model | |
| 1 | 202 | 1084.4 | 0.2082 | 0.1365 | 1.0 | -6.23 | 20.6 | ASHRAETau |
| 2 | 202 | 1084.4 | 0.2082 | 0.1365 | 1.0 | -6.23 | 20.6 | ASHRAETau |
| 3 | 202 | 1084.4 | 0.2082 | 0.1365 | 1.0 | -6.23 | 20.6 | ASHRAETau |
| 4 | 202 | 1084.4 | 0.2082 | 0.1365 | 1.0 | -6.23 | 20.6 | ASHRAETau |
| 5 | 21 | 1229.0 | 0.1415 | 5.7310E-002 | 1.0 | -11.15 | -20.1 | ASHRAEClearSky |
| 6 | 21 | 1229.0 | 0.1415 | 5.7310E-002 | 1.0 | -11.15 | -20.1 | ASHRAEClearSky |
| 7 | 21 | 1229.0 | 0.1415 | 5.7310E-002 | 1.0 | -11.15 | -20.1 | ASHRAEClearSky |
| Zone Name | Environment Type/Name | Average Warmup Temperature Difference {deltaC} | Std Dev Warmup Temperature Difference {deltaC} | Max Temperature Pass/Fail Convergence | Min Temperature Pass/Fail Convergence | Average Warmup Load Difference {W} | Std Dev Warmup Load Difference {W} | Heating Load Pass/Fail Convergence | Cooling Load Pass/Fail Convergence | |
| 1 | 01_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 5.5930260292E-005 | 1.1800151803E-004 | Pass | Pass | 3.4406474845E-002 | 6.5335606423E-002 | Pass | Pass |
| 2 | 01_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 4.0309548226E-005 | 8.1688069490E-005 | Pass | Pass | 2.5575419360E-002 | 5.1747883255E-002 | Pass | Pass |
| 3 | 01_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 6.8305167880E-003 | 1.7967545393E-002 | Pass | Pass | 6.7970836798E-002 | 0.2060444171 | Pass | Pass |
| 4 | 01_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 1.0315086077E-002 | 2.8211232673E-002 | Pass | Pass | 7.6807915793E-002 | 0.3902213916 | Pass | Pass |
| 5 | 02_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 3.4022028484E-005 | 6.0711289641E-005 | Pass | Pass | 1.7455197992E-002 | 2.9885853158E-002 | Pass | Pass |
| 6 | 02_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 4.2002284739E-005 | 7.0247152677E-005 | Pass | Pass | 1.6785307805E-002 | 2.7432371262E-002 | Pass | Pass |
| 7 | 02_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 2.7008430000E-005 | 4.6464920081E-005 | Pass | Pass | 1.9123738971E-002 | 2.9338742323E-002 | Pass | Pass |
| 8 | 02_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 3.5556478831E-005 | 5.5443017547E-005 | Pass | Pass | 2.0047691332E-002 | 3.0275898019E-002 | Pass | Pass |
| 9 | 03_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 3.3959627701E-005 | 6.3564124939E-005 | Pass | Pass | 1.8947031100E-002 | 3.3424038051E-002 | Pass | Pass |
| 10 | 03_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 2.6949486051E-005 | 5.0854426969E-005 | Pass | Pass | 1.7781131699E-002 | 3.1564864329E-002 | Pass | Pass |
| 11 | 03_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 2.5220972653E-005 | 4.4439679111E-005 | Pass | Pass | 2.0737091204E-002 | 3.2754565737E-002 | Pass | Pass |
| 12 | 03_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 3.4284435664E-005 | 5.4648009387E-005 | Pass | Pass | 2.1647279260E-002 | 3.3597135071E-002 | Pass | Pass |
| 13 | 01_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 1.0670420663E-003 | 4.1748434160E-003 | Pass | Pass | 3.7857189076E-002 | 7.5784529295E-002 | Pass | Pass |
| 14 | 01_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 4.6723994344E-005 | 9.8449454399E-005 | Pass | Pass | 2.7798956733E-002 | 5.6723880560E-002 | Pass | Pass |
| 15 | 01_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 1.7773529359E-002 | 3.2593826613E-002 | Pass | Pass | 4.7740593611E-002 | 0.1410582098 | Pass | Pass |
| 16 | 01_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 1.9963077574E-002 | 4.3967782656E-002 | Pass | Pass | 4.5165802872E-002 | 0.1186210821 | Pass | Pass |
| 17 | 02_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 3.4394457163E-005 | 7.1324466925E-005 | Pass | Pass | 1.8426178130E-002 | 3.1529503204E-002 | Pass | Pass |
| 18 | 02_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 4.3535794425E-005 | 8.1943758417E-005 | Pass | Pass | 1.7845078166E-002 | 2.9181009444E-002 | Pass | Pass |
| 19 | 02_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 2.7522674119E-005 | 5.2911535838E-005 | Pass | Pass | 2.1116094607E-002 | 3.2204534727E-002 | Pass | Pass |
| 20 | 02_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 3.6149617849E-005 | 6.2359758272E-005 | Pass | Pass | 2.2044708985E-002 | 3.3227942297E-002 | Pass | Pass |
| 21 | 03_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 3.5219623571E-005 | 7.4553883607E-005 | Pass | Pass | 2.0281113624E-002 | 3.5817469020E-002 | Pass | Pass |
| 22 | 03_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 2.8016609012E-005 | 5.9020159315E-005 | Pass | Pass | 1.9385510506E-002 | 3.4561735734E-002 | Pass | Pass |
| 23 | 03_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 2.5849893831E-005 | 5.0327462237E-005 | Pass | Pass | 2.3268012899E-002 | 3.6938735052E-002 | Pass | Pass |
| 24 | 03_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 3.5359672297E-005 | 6.1429279666E-005 | Pass | Pass | 2.4246635850E-002 | 3.7935484788E-002 | Pass | Pass |
| 25 | 01_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 8.4598608613E-005 | 1.8107855052E-004 | Pass | Pass | 3.5657112578E-002 | 6.7608100900E-002 | Pass | Pass |
| 26 | 01_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 5.9919810661E-005 | 1.2669819224E-004 | Pass | Pass | 2.6088914382E-002 | 5.2897867685E-002 | Pass | Pass |
| 27 | 01_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 9.7535405372E-003 | 2.1751717426E-002 | Pass | Pass | 5.9951213219E-002 | 0.1933076953 | Pass | Pass |
| 28 | 01_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 1.2942224421E-002 | 3.2986163431E-002 | Pass | Pass | 6.0539252894E-002 | 0.2393517920 | Pass | Pass |
| 29 | 02_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 4.2776886467E-005 | 9.0501701207E-005 | Pass | Pass | 1.7696937126E-002 | 3.0302548486E-002 | Pass | Pass |
| 30 | 02_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 5.2817629607E-005 | 1.0491364650E-004 | Pass | Pass | 1.7053715751E-002 | 2.7875585941E-002 | Pass | Pass |
| 31 | 02_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 3.3090537317E-005 | 6.5299874264E-005 | Pass | Pass | 1.9604161447E-002 | 3.0028295581E-002 | Pass | Pass |
| 32 | 02_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 4.1435489662E-005 | 7.5055531720E-005 | Pass | Pass | 2.0529053872E-002 | 3.0988568282E-002 | Pass | Pass |
| 33 | 03_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 4.4717490735E-005 | 9.4502013819E-005 | Pass | Pass | 1.9268470858E-002 | 3.3998148347E-002 | Pass | Pass |
| 34 | 03_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 3.4859913226E-005 | 7.5698987341E-005 | Pass | Pass | 1.8175898650E-002 | 3.2283476037E-002 | Pass | Pass |
| 35 | 03_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 3.1580844185E-005 | 6.2138262276E-005 | Pass | Pass | 2.1333919662E-002 | 3.3709527196E-002 | Pass | Pass |
| 36 | 03_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 4.0847650893E-005 | 7.3598174587E-005 | Pass | Pass | 2.2244760987E-002 | 3.4578961195E-002 | Pass | Pass |
| 37 | 01_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 6.6059847339E-005 | 1.4097232961E-004 | Pass | Pass | 3.5765149374E-002 | 6.7810335151E-002 | Pass | Pass |
| 38 | 01_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 4.5411885612E-005 | 9.4105122439E-005 | Pass | Pass | 2.6122162711E-002 | 5.2979463632E-002 | Pass | Pass |
| 39 | 01_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 9.9210443608E-003 | 2.2259654711E-002 | Pass | Pass | 6.0274381435E-002 | 0.1978249413 | Pass | Pass |
| 40 | 01_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 1.3091905592E-002 | 3.3336301344E-002 | Pass | Pass | 6.0093072384E-002 | 0.2339756736 | Pass | Pass |
| 41 | 02_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 3.6209185697E-005 | 7.0903207452E-005 | Pass | Pass | 1.7717007253E-002 | 3.0334987934E-002 | Pass | Pass |
| 42 | 02_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 4.3558226344E-005 | 8.0396556291E-005 | Pass | Pass | 1.7068647603E-002 | 2.7910936282E-002 | Pass | Pass |
| 43 | 02_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 2.7872199037E-005 | 5.1887997061E-005 | Pass | Pass | 1.9634632793E-002 | 3.0090107484E-002 | Pass | Pass |
| 44 | 02_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 3.7754359927E-005 | 6.2364459372E-005 | Pass | Pass | 2.0570330728E-002 | 3.1053962962E-002 | Pass | Pass |
| 45 | 03_A1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 3.6835646350E-005 | 7.4236750927E-005 | Pass | Pass | 1.9295963114E-002 | 3.4057796829E-002 | Pass | Pass |
| 46 | 03_A2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 2.7991421239E-005 | 5.8411243359E-005 | Pass | Pass | 1.8198380960E-002 | 3.2351088721E-002 | Pass | Pass |
| 47 | 03_B2 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 2.6242444396E-005 | 4.9530471017E-005 | Pass | Pass | 2.1374229978E-002 | 3.3813854850E-002 | Pass | Pass |
| 48 | 03_C1 | SizingPeriod: ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 3.6640458687E-005 | 6.1631744485E-005 | Pass | Pass | 2.2300810523E-002 | 3.4690347526E-002 | Pass | Pass |
| 49 | 01_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 8.9435849274E-002 | 8.7240284842E-002 | Pass | Pass | 4.1595750494E-003 | 7.4766501458E-003 | Pass | Pass |
| 50 | 01_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.1213243451 | 0.1237457063 | Pass | Pass | 9.9274475529E-003 | 1.5617799900E-002 | Pass | Pass |
| 51 | 01_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 6.3409494954E-002 | 6.5780382291E-002 | Pass | Pass | 4.4986480958E-003 | 7.8743330445E-003 | Pass | Pass |
| 52 | 01_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 5.8316388814E-002 | 6.0860606729E-002 | Pass | Pass | 3.1762547852E-003 | 5.5502970419E-003 | Pass | Pass |
| 53 | 02_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 7.3601093600E-002 | 6.9965882047E-002 | Pass | Pass | 5.4720502410E-003 | 9.5524480770E-003 | Pass | Pass |
| 54 | 02_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.1011086724 | 0.1095298774 | Pass | Pass | 9.8075641928E-003 | 1.5729600404E-002 | Pass | Pass |
| 55 | 02_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 5.2514654184E-002 | 5.1888089717E-002 | Pass | Pass | 6.5260740266E-003 | 1.1180811511E-002 | Pass | Pass |
| 56 | 02_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 4.8245053264E-002 | 4.7036860149E-002 | Pass | Pass | 5.2990225344E-003 | 8.9826784440E-003 | Pass | Pass |
| 57 | 03_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 8.5030123231E-002 | 7.9439243284E-002 | Pass | Pass | 5.8060043506E-003 | 1.0228435734E-002 | Pass | Pass |
| 58 | 03_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 8.3900289740E-002 | 7.8746110732E-002 | Pass | Pass | 6.8510076478E-003 | 1.2121311265E-002 | Pass | Pass |
| 59 | 03_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 6.1081094359E-002 | 6.0460122798E-002 | Pass | Pass | 7.5405440458E-003 | 1.3040898438E-002 | Pass | Pass |
| 60 | 03_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 5.6214803870E-002 | 5.4912062870E-002 | Pass | Pass | 6.0716443732E-003 | 1.0360892806E-002 | Pass | Pass |
| 61 | 01_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 2.5093427236E-002 | 4.5239181355E-002 | Pass | Pass | 2.4008899090E-002 | 6.8045028768E-002 | Pass | Pass |
| 62 | 01_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 2.1876896125E-002 | 4.6869993125E-002 | Pass | Pass | 2.4368999837E-002 | 6.8092666456E-002 | Pass | Pass |
| 63 | 01_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 4.1400021301E-002 | 5.3503766454E-002 | Pass | Pass | 2.4216861796E-002 | 8.5042747254E-002 | Pass | Pass |
| 64 | 01_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 4.1164732411E-002 | 5.3594959859E-002 | Pass | Pass | 2.0507347429E-002 | 6.8420629977E-002 | Pass | Pass |
| 65 | 02_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 2.1750478854E-005 | 4.6241082636E-005 | Pass | Pass | 1.7114862382E-002 | 4.0237025949E-002 | Pass | Pass |
| 66 | 02_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 2.7025917094E-005 | 5.2122044100E-005 | Pass | Pass | 1.7721959767E-002 | 4.0459587176E-002 | Pass | Pass |
| 67 | 02_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 1.4467555062E-005 | 3.4923455940E-005 | Pass | Pass | 2.4067746694E-002 | 5.6110111830E-002 | Pass | Pass |
| 68 | 02_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 1.8480382148E-005 | 4.4999658084E-005 | Pass | Pass | 2.3464801330E-002 | 5.2970301542E-002 | Pass | Pass |
| 69 | 03_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 2.1229133827E-005 | 4.8229547822E-005 | Pass | Pass | 1.8739896522E-002 | 4.7533680187E-002 | Pass | Pass |
| 70 | 03_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 1.5855708971E-005 | 3.7321704734E-005 | Pass | Pass | 2.0103259248E-002 | 5.2471580334E-002 | Pass | Pass |
| 71 | 03_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 1.3255597169E-005 | 3.3671266361E-005 | Pass | Pass | 2.6573926176E-002 | 6.8755380956E-002 | Pass | Pass |
| 72 | 03_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | 1.7244936703E-005 | 4.4123675298E-005 | Pass | Pass | 2.5982999103E-002 | 6.4842074885E-002 | Pass | Pass |
| 73 | 01_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 7.1436664602E-002 | 8.1023172268E-002 | Pass | Pass | 1.0017510939E-002 | 3.0865371363E-002 | Pass | Pass |
| 74 | 01_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 9.3624213000E-002 | 0.1083495653 | Pass | Pass | 1.3963619732E-002 | 2.9480555104E-002 | Pass | Pass |
| 75 | 01_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 6.3380584045E-002 | 6.4908230704E-002 | Pass | Pass | 4.7303430607E-003 | 8.4542004184E-003 | Pass | Pass |
| 76 | 01_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 5.8359411459E-002 | 6.0041775220E-002 | Pass | Pass | 3.3598585064E-003 | 5.9592263682E-003 | Pass | Pass |
| 77 | 02_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 1.9210537107E-002 | 3.1268753986E-002 | Pass | Pass | 1.7219514368E-002 | 4.6139284412E-002 | Pass | Pass |
| 78 | 02_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 4.2705787853E-002 | 5.1618915012E-002 | Pass | Pass | 1.5507478658E-002 | 4.0217589809E-002 | Pass | Pass |
| 79 | 02_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 5.0226646325E-002 | 5.1523461142E-002 | Pass | Pass | 9.9784596000E-003 | 2.3602685906E-002 | Pass | Pass |
| 80 | 02_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 4.3365944874E-002 | 4.6860722350E-002 | Pass | Pass | 1.0807648938E-002 | 2.9498623154E-002 | Pass | Pass |
| 81 | 03_A1 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 3.3486278595E-002 | 4.0573773602E-002 | Pass | Pass | 1.6289324382E-002 | 4.8596483386E-002 | Pass | Pass |
| 82 | 03_A2 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 4.5023481556E-002 | 5.0149857054E-002 | Pass | Pass | 1.5265147960E-002 | 5.3148798581E-002 | Pass | Pass |
| 83 | 03_B2 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 6.1010353630E-002 | 5.9686627671E-002 | Pass | Pass | 7.6833677148E-003 | 1.3533432325E-002 | Pass | Pass |
| 84 | 03_C1 | SizingPeriod: ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 5.5568500004E-002 | 5.4335373796E-002 | Pass | Pass | 6.3046086518E-003 | 1.0848111968E-002 | Pass | Pass |
| 85 | 01_A1 | RunPeriod: RUN PERIOD 1 | 0.1514487740 | 0.2795989057 | Pass | Pass | 4.1123701324E-002 | 0.1103388275 | Pass | Pass |
| 86 | 01_A2 | RunPeriod: RUN PERIOD 1 | 0.1902991607 | 0.5528823100 | Pass | Pass | 6.5122023941E-002 | 0.1678680644 | Pass | Pass |
| 87 | 01_B2 | RunPeriod: RUN PERIOD 1 | 0.1410063817 | 0.2562833970 | Pass | Pass | 6.1412674093E-002 | 0.2424370657 | Pass | Pass |
| 88 | 01_C1 | RunPeriod: RUN PERIOD 1 | 0.1199882861 | 0.1814151867 | Pass | Pass | 4.5612926481E-002 | 0.1670738565 | Pass | Pass |
| 89 | 02_A1 | RunPeriod: RUN PERIOD 1 | 0.1253474926 | 0.3041432648 | Pass | Pass | 7.3251565323E-002 | 0.2165205248 | Pass | Pass |
| 90 | 02_A2 | RunPeriod: RUN PERIOD 1 | 0.1863136321 | 0.5613773238 | Pass | Pass | 6.4317698217E-002 | 0.1725328789 | Pass | Pass |
| 91 | 02_B2 | RunPeriod: RUN PERIOD 1 | 0.1174028433 | 0.2769005494 | Pass | Pass | 8.5227326934E-002 | 0.2672539489 | Pass | Pass |
| 92 | 02_C1 | RunPeriod: RUN PERIOD 1 | 0.1082854409 | 0.2335543477 | Pass | Pass | 7.5928292690E-002 | 0.2402367381 | Pass | Pass |
| 93 | 03_A1 | RunPeriod: RUN PERIOD 1 | 0.1487378648 | 0.3358656609 | Pass | Pass | 7.7064956168E-002 | 0.2304307411 | Pass | Pass |
| 94 | 03_A2 | RunPeriod: RUN PERIOD 1 | 0.1716172671 | 0.3836412645 | Pass | Pass | 8.6361876350E-002 | 0.2609955017 | Pass | Pass |
| 95 | 03_B2 | RunPeriod: RUN PERIOD 1 | 0.1433608609 | 0.3221293894 | Pass | Pass | 9.5608393998E-002 | 0.3105476290 | Pass | Pass |
| 96 | 03_C1 | RunPeriod: RUN PERIOD 1 | 0.1323338976 | 0.2679974408 | Pass | Pass | 8.6574836564E-002 | 0.2868975970 | Pass | Pass |
Report: Climatic Data Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
SizingPeriod:DesignDay| Maximum Dry Bulb [C] | Daily Temperature Range [deltaC] | Humidity Value | Humidity Type | Wind Speed [m/s] | Wind Direction | |
| ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 23.20 | 7.50 | 14.70 | Wetbulb [C] | 3.80 | 260.00 |
| ANCHORAGEELMENDORFANNCLG.4CONDNSDPMDB | 16.40 | 7.50 | 13.80 | Dewpoint [C] | 3.80 | 260.00 |
| ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 21.30 | 7.50 | 44300.00 | Enthalpy [J/kg] | 3.80 | 260.00 |
| ANCHORAGEELMENDORFANNCLG.4CONDNSWBMDB | 21.20 | 7.50 | 15.80 | Wetbulb [C] | 3.80 | 260.00 |
| ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | -26.00 | 0.00 | -26.00 | Wetbulb [C] | 2.20 | 50.00 |
| ANCHORAGEELMENDORFANNHTGWIND99.6CONDNSWSMCDB | -3.10 | 0.00 | -3.10 | Wetbulb [C] | 10.20 | 50.00 |
| ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | -23.70 | 0.00 | -29.90 | Dewpoint [C] | 2.20 | 50.00 |
| Value | |
| None |
Report: Envelope Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Opaque Exterior| Construction | Reflectance | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Net Area [m2] | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| SURFACE 10 | WW300B | 0.30 | 0.265 | 0.276 | 26.40 | 26.40 | 180.00 | 90.00 | S |
| SURFACE 12 | WW300B | 0.30 | 0.265 | 0.276 | 5.62 | 3.67 | 0.00 | 90.00 | N |
| SURFACE 14 | WW300B | 0.30 | 0.265 | 0.276 | 24.53 | 18.22 | 90.00 | 90.00 | E |
| SURFACE 9 | EXTSLABCARPET 4IN CLIMATEZONE 1-8 | 0.15 | 2.945 | 5.634 | 57.60 | 57.60 | 0.00 | 180.00 | |
| SURFACE 2 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 9.51 | 270.00 | 90.00 | W |
| SURFACE 3 | WW300B | 0.30 | 0.265 | 0.276 | 30.66 | 28.71 | 0.00 | 90.00 | N |
| SURFACE 5 | WW300B | 0.30 | 0.265 | 0.276 | 26.40 | 26.40 | 180.00 | 90.00 | S |
| SURFACE 6 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 10.41 | 270.00 | 90.00 | W |
| SURFACE 7 | WW300B | 0.30 | 0.265 | 0.276 | 4.26 | 2.03 | 180.00 | 90.00 | S |
| SURFACE 1 | EXTSLABCARPET 4IN CLIMATEZONE 1-8 | 0.15 | 2.945 | 5.634 | 62.25 | 62.25 | 0.00 | 180.00 | |
| SURFACE 28 | WW300B | 0.30 | 0.265 | 0.276 | 12.77 | 10.02 | 270.00 | 90.00 | W |
| SURFACE 29 | WW300B | 0.30 | 0.265 | 0.276 | 11.67 | 7.21 | 0.00 | 90.00 | N |
| SURFACE 30 | WW300B | 0.30 | 0.265 | 0.276 | 2.04 | 2.04 | 270.00 | 90.00 | W |
| SURFACE 31 | WW300B | 0.30 | 0.265 | 0.276 | 20.01 | 17.73 | 0.00 | 90.00 | N |
| SURFACE 33 | WW300B | 0.30 | 0.265 | 0.276 | 30.66 | 28.71 | 180.00 | 90.00 | S |
| SURFACE 34 | WW300B | 0.30 | 0.265 | 0.276 | 20.95 | 17.25 | 270.00 | 90.00 | W |
| SURFACE 35 | WW300B | 0.30 | 0.265 | 0.276 | 1.02 | 1.02 | 180.00 | 90.00 | S |
| SURFACE 27 | EXTSLABCARPET 4IN CLIMATEZONE 1-8 | 0.15 | 2.945 | 5.634 | 96.77 | 96.77 | 0.00 | 180.00 | |
| SURFACE 17 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 11.12 | 90.00 | 90.00 | E |
| SURFACE 18 | WW300B | 0.30 | 0.265 | 0.276 | 6.13 | 3.90 | 0.00 | 90.00 | N |
| SURFACE 19 | WW300B | 0.30 | 0.265 | 0.276 | 33.72 | 25.46 | 90.00 | 90.00 | E |
| SURFACE 20 | WW300B | 0.30 | 0.265 | 0.276 | 4.26 | 4.26 | 180.00 | 90.00 | S |
| SURFACE 22 | WW300B | 0.30 | 0.265 | 0.276 | 10.22 | 10.22 | 270.00 | 90.00 | W |
| SURFACE 23 | WW300B | 0.30 | 0.265 | 0.276 | 5.62 | 3.67 | 180.00 | 90.00 | S |
| SURFACE 25 | WW300B | 0.30 | 0.265 | 0.276 | 24.53 | 21.54 | 0.00 | 90.00 | N |
| SURFACE 16 | EXTSLABCARPET 4IN CLIMATEZONE 1-8 | 0.15 | 2.945 | 5.634 | 113.62 | 113.62 | 180.00 | 180.00 | |
| SURFACE 46 | WW300B | 0.30 | 0.265 | 0.276 | 26.40 | 26.40 | 180.00 | 90.00 | S |
| SURFACE 48 | WW300B | 0.30 | 0.265 | 0.276 | 5.62 | 3.67 | 0.00 | 90.00 | N |
| SURFACE 50 | WW300B | 0.30 | 0.265 | 0.276 | 24.53 | 17.73 | 90.00 | 90.00 | E |
| SURFACE 38 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 8.79 | 270.00 | 90.00 | W |
| SURFACE 39 | WW300B | 0.30 | 0.265 | 0.276 | 30.66 | 28.71 | 0.00 | 90.00 | N |
| SURFACE 41 | WW300B | 0.30 | 0.265 | 0.276 | 26.40 | 26.40 | 180.00 | 90.00 | S |
| SURFACE 42 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 10.41 | 270.00 | 90.00 | W |
| SURFACE 43 | WW300B | 0.30 | 0.265 | 0.276 | 4.26 | 2.03 | 180.00 | 90.00 | S |
| SURFACE 64 | WW300B | 0.30 | 0.265 | 0.276 | 12.77 | 9.30 | 270.00 | 90.00 | W |
| SURFACE 65 | WW300B | 0.30 | 0.265 | 0.276 | 11.67 | 7.21 | 0.00 | 90.00 | N |
| SURFACE 66 | WW300B | 0.30 | 0.265 | 0.276 | 2.04 | 2.04 | 270.00 | 90.00 | W |
| SURFACE 67 | WW300B | 0.30 | 0.265 | 0.276 | 20.01 | 17.13 | 0.00 | 90.00 | N |
| SURFACE 69 | WW300B | 0.30 | 0.265 | 0.276 | 30.66 | 28.71 | 180.00 | 90.00 | S |
| SURFACE 70 | WW300B | 0.30 | 0.265 | 0.276 | 20.95 | 16.28 | 270.00 | 90.00 | W |
| SURFACE 71 | WW300B | 0.30 | 0.265 | 0.276 | 1.02 | 1.02 | 180.00 | 90.00 | S |
| SURFACE 53 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 11.12 | 90.00 | 90.00 | E |
| SURFACE 54 | WW300B | 0.30 | 0.265 | 0.276 | 6.13 | 3.90 | 0.00 | 90.00 | N |
| SURFACE 55 | WW300B | 0.30 | 0.265 | 0.276 | 33.72 | 23.29 | 90.00 | 90.00 | E |
| SURFACE 56 | WW300B | 0.30 | 0.265 | 0.276 | 4.26 | 4.26 | 180.00 | 90.00 | S |
| SURFACE 58 | WW300B | 0.30 | 0.265 | 0.276 | 10.22 | 10.22 | 270.00 | 90.00 | W |
| SURFACE 59 | WW300B | 0.30 | 0.265 | 0.276 | 5.62 | 3.67 | 180.00 | 90.00 | S |
| SURFACE 61 | WW300B | 0.30 | 0.265 | 0.276 | 24.53 | 20.75 | 0.00 | 90.00 | N |
| SURFACE 82 | WW300B | 0.30 | 0.265 | 0.276 | 26.40 | 26.40 | 180.00 | 90.00 | S |
| SURFACE 84 | WW300B | 0.30 | 0.265 | 0.276 | 5.62 | 3.67 | 0.00 | 90.00 | N |
| SURFACE 86 | WW300B | 0.30 | 0.265 | 0.276 | 24.53 | 17.73 | 90.00 | 90.00 | E |
| SURFACE 87 | R703 1 | 0.30 | 0.102 | 0.104 | 57.60 | 57.60 | 0.00 | 0.00 | |
| SURFACE 74 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 8.79 | 270.00 | 90.00 | W |
| SURFACE 75 | WW300B | 0.30 | 0.265 | 0.276 | 30.66 | 28.71 | 0.00 | 90.00 | N |
| SURFACE 77 | WW300B | 0.30 | 0.265 | 0.276 | 26.40 | 26.40 | 180.00 | 90.00 | S |
| SURFACE 78 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 10.41 | 270.00 | 90.00 | W |
| SURFACE 79 | WW300B | 0.30 | 0.265 | 0.276 | 4.26 | 2.03 | 180.00 | 90.00 | S |
| SURFACE 80 | R703 1 | 0.30 | 0.102 | 0.104 | 62.25 | 62.25 | 0.00 | 0.00 | |
| SURFACE 100 | WW300B | 0.30 | 0.265 | 0.276 | 12.77 | 9.30 | 270.00 | 90.00 | W |
| SURFACE 101 | WW300B | 0.30 | 0.265 | 0.276 | 11.67 | 7.21 | 0.00 | 90.00 | N |
| SURFACE 102 | WW300B | 0.30 | 0.265 | 0.276 | 2.04 | 2.04 | 270.00 | 90.00 | W |
| SURFACE 103 | WW300B | 0.30 | 0.265 | 0.276 | 20.01 | 17.13 | 0.00 | 90.00 | N |
| SURFACE 105 | WW300B | 0.30 | 0.265 | 0.276 | 30.66 | 28.71 | 180.00 | 90.00 | S |
| SURFACE 106 | WW300B | 0.30 | 0.265 | 0.276 | 20.95 | 16.28 | 270.00 | 90.00 | W |
| SURFACE 107 | WW300B | 0.30 | 0.265 | 0.276 | 1.02 | 1.02 | 180.00 | 90.00 | S |
| SURFACE 108 | R703 1 | 0.30 | 0.102 | 0.104 | 96.77 | 96.77 | 0.00 | 0.00 | |
| SURFACE 89 | WW300B | 0.30 | 0.265 | 0.276 | 12.26 | 11.12 | 90.00 | 90.00 | E |
| SURFACE 90 | WW300B | 0.30 | 0.265 | 0.276 | 6.13 | 3.90 | 0.00 | 90.00 | N |
| SURFACE 91 | WW300B | 0.30 | 0.265 | 0.276 | 33.72 | 23.29 | 90.00 | 90.00 | E |
| SURFACE 92 | WW300B | 0.30 | 0.265 | 0.276 | 4.26 | 4.26 | 180.00 | 90.00 | S |
| SURFACE 94 | WW300B | 0.30 | 0.265 | 0.276 | 10.22 | 10.22 | 270.00 | 90.00 | W |
| SURFACE 95 | WW300B | 0.30 | 0.265 | 0.276 | 5.62 | 3.67 | 180.00 | 90.00 | S |
| SURFACE 97 | WW300B | 0.30 | 0.265 | 0.276 | 24.53 | 20.75 | 0.00 | 90.00 | N |
| SURFACE 98 | R703 1 | 0.30 | 0.102 | 0.104 | 113.62 | 113.62 | 0.00 | 0.00 |
| Construction | Glass Area [m2] | Frame Area [m2] | Divider Area [m2] | Area of One Opening [m2] | Area of Multiplied Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Frame Conductance [W/m2-K] | Divider Conductance [W/m2-K] | Shade Control | Parent Surface | Azimuth [deg] | Tilt [deg] | Cardinal Direction | |
| SUB SURFACE 51 | KATERRATYPICALWINDOWRESIDENTIAL | 4.46 | 0.00 | 0.00 | 4.46 | 4.46 | 1.362 | 0.452 | 0.501 | No | SURFACE 14 | 90.00 | 90.00 | E | ||
| SUB SURFACE 54 | KATERRATYPICALWINDOWRESIDENTIAL | 1.85 | 0.00 | 0.00 | 1.85 | 1.85 | 1.362 | 0.452 | 0.501 | No | SURFACE 14 | 90.00 | 90.00 | E | ||
| SUB SURFACE 42 | KATERRATYPICALWINDOWRESIDENTIAL | 2.75 | 0.00 | 0.00 | 2.75 | 2.75 | 1.362 | 0.452 | 0.501 | No | SURFACE 2 | 270.00 | 90.00 | W | ||
| SUB SURFACE 48 | KATERRATYPICALWINDOWRESIDENTIAL | 1.85 | 0.00 | 0.00 | 1.85 | 1.85 | 1.362 | 0.452 | 0.501 | No | SURFACE 6 | 270.00 | 90.00 | W | ||
| SUB SURFACE 45 | KATERRATYPICALWINDOWRESIDENTIAL | 2.23 | 0.00 | 0.00 | 2.23 | 2.23 | 1.362 | 0.452 | 0.501 | No | SURFACE 7 | 180.00 | 90.00 | S | ||
| SUB SURFACE 37 | KATERRATYPICALWINDOWRESIDENTIAL | 2.75 | 0.00 | 0.00 | 2.75 | 2.75 | 1.362 | 0.452 | 0.501 | No | SURFACE 28 | 270.00 | 90.00 | W | ||
| SUB SURFACE 30 | KATERRATYPICALWINDOWRESIDENTIAL | 4.46 | 0.00 | 0.00 | 4.46 | 4.46 | 1.362 | 0.452 | 0.501 | No | SURFACE 29 | 0.00 | 90.00 | N | ||
| SUB SURFACE 26 | KATERRATYPICALWINDOWRESIDENTIAL | 1.14 | 0.00 | 0.00 | 1.14 | 1.14 | 1.362 | 0.452 | 0.501 | No | SURFACE 31 | 0.00 | 90.00 | N | ||
| SUB SURFACE 27 | KATERRATYPICALWINDOWRESIDENTIAL | 1.14 | 0.00 | 0.00 | 1.14 | 1.14 | 1.362 | 0.452 | 0.501 | No | SURFACE 31 | 0.00 | 90.00 | N | ||
| SUB SURFACE 38 | KATERRATYPICALWINDOWRESIDENTIAL | 1.85 | 0.00 | 0.00 | 1.85 | 1.85 | 1.362 | 0.452 | 0.501 | No | SURFACE 34 | 270.00 | 90.00 | W | ||
| SUB SURFACE 39 | KATERRATYPICALWINDOWRESIDENTIAL | 1.85 | 0.00 | 0.00 | 1.85 | 1.85 | 1.362 | 0.452 | 0.501 | No | SURFACE 34 | 270.00 | 90.00 | W | ||
| SUB SURFACE 6 | KATERRATYPICALWINDOWRESIDENTIAL | 1.14 | 0.00 | 0.00 | 1.14 | 1.14 | 1.362 | 0.452 | 0.501 | No | SURFACE 17 | 90.00 | 90.00 | E | ||
| SUB SURFACE 3 | KATERRATYPICALWINDOWRESIDENTIAL | 2.23 | 0.00 | 0.00 | 2.23 | 2.23 | 1.362 | 0.452 | 0.501 | No | SURFACE 18 | 0.00 | 90.00 | N | ||
| SUB SURFACE 13 | KATERRATYPICALWINDOWRESIDENTIAL | 2.75 | 0.00 | 0.00 | 2.75 | 2.75 | 1.362 | 0.452 | 0.501 | No | SURFACE 19 | 90.00 | 90.00 | E | ||
| SUB SURFACE 14 | KATERRATYPICALWINDOWRESIDENTIAL | 2.75 | 0.00 | 0.00 | 2.75 | 2.75 | 1.362 | 0.452 | 0.501 | No | SURFACE 19 | 90.00 | 90.00 | E | ||
| SUB SURFACE 15 | KATERRATYPICALWINDOWRESIDENTIAL | 2.75 | 0.00 | 0.00 | 2.75 | 2.75 | 1.362 | 0.452 | 0.501 | No | SURFACE 19 | 90.00 | 90.00 | E | ||
| SUB SURFACE 18 | KATERRATYPICALWINDOWRESIDENTIAL | 1.14 | 0.00 | 0.00 | 1.14 | 1.14 | 1.362 | 0.452 | 0.501 | No | SURFACE 25 | 0.00 | 90.00 | N | ||
| SUB SURFACE 19 | KATERRATYPICALWINDOWRESIDENTIAL | 1.85 | 0.00 | 0.00 | 1.85 | 1.85 | 1.362 | 0.452 | 0.501 | No | SURFACE 25 | 0.00 | 90.00 | N | ||
| SUB SURFACE 50 | KATERRATYPICALWINDOWRESIDENTIAL | 4.46 | 0.00 | 0.00 | 4.46 | 4.46 | 1.362 | 0.452 | 0.501 | No | SURFACE 50 | 90.00 | 90.00 | E | ||
| SUB SURFACE 53 | KATERRATYPICALWINDOWRESIDENTIAL | 2.33 | 0.00 | 0.00 | 2.33 | 2.33 | 1.362 | 0.452 | 0.501 | No | SURFACE 50 | 90.00 | 90.00 | E | ||
| SUB SURFACE 41 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 38 | 270.00 | 90.00 | W | ||
| SUB SURFACE 47 | KATERRATYPICALWINDOWRESIDENTIAL | 1.85 | 0.00 | 0.00 | 1.85 | 1.85 | 1.362 | 0.452 | 0.501 | No | SURFACE 42 | 270.00 | 90.00 | W | ||
| SUB SURFACE 44 | KATERRATYPICALWINDOWRESIDENTIAL | 2.23 | 0.00 | 0.00 | 2.23 | 2.23 | 1.362 | 0.452 | 0.501 | No | SURFACE 43 | 180.00 | 90.00 | S | ||
| SUB SURFACE 34 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 64 | 270.00 | 90.00 | W | ||
| SUB SURFACE 29 | KATERRATYPICALWINDOWRESIDENTIAL | 4.46 | 0.00 | 0.00 | 4.46 | 4.46 | 1.362 | 0.452 | 0.501 | No | SURFACE 65 | 0.00 | 90.00 | N | ||
| SUB SURFACE 24 | KATERRATYPICALWINDOWRESIDENTIAL | 1.44 | 0.00 | 0.00 | 1.44 | 1.44 | 1.362 | 0.452 | 0.501 | No | SURFACE 67 | 0.00 | 90.00 | N | ||
| SUB SURFACE 25 | KATERRATYPICALWINDOWRESIDENTIAL | 1.44 | 0.00 | 0.00 | 1.44 | 1.44 | 1.362 | 0.452 | 0.501 | No | SURFACE 67 | 0.00 | 90.00 | N | ||
| SUB SURFACE 35 | KATERRATYPICALWINDOWRESIDENTIAL | 2.33 | 0.00 | 0.00 | 2.33 | 2.33 | 1.362 | 0.452 | 0.501 | No | SURFACE 70 | 270.00 | 90.00 | W | ||
| SUB SURFACE 36 | KATERRATYPICALWINDOWRESIDENTIAL | 2.33 | 0.00 | 0.00 | 2.33 | 2.33 | 1.362 | 0.452 | 0.501 | No | SURFACE 70 | 270.00 | 90.00 | W | ||
| SUB SURFACE 5 | KATERRATYPICALWINDOWRESIDENTIAL | 1.14 | 0.00 | 0.00 | 1.14 | 1.14 | 1.362 | 0.452 | 0.501 | No | SURFACE 53 | 90.00 | 90.00 | E | ||
| SUB SURFACE 2 | KATERRATYPICALWINDOWRESIDENTIAL | 2.23 | 0.00 | 0.00 | 2.23 | 2.23 | 1.362 | 0.452 | 0.501 | No | SURFACE 54 | 0.00 | 90.00 | N | ||
| SUB SURFACE 10 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 55 | 90.00 | 90.00 | E | ||
| SUB SURFACE 11 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 55 | 90.00 | 90.00 | E | ||
| SUB SURFACE 12 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 55 | 90.00 | 90.00 | E | ||
| SUB SURFACE 17 | KATERRATYPICALWINDOWRESIDENTIAL | 1.44 | 0.00 | 0.00 | 1.44 | 1.44 | 1.362 | 0.452 | 0.501 | No | SURFACE 61 | 0.00 | 90.00 | N | ||
| SUB SURFACE 20 | KATERRATYPICALWINDOWRESIDENTIAL | 2.33 | 0.00 | 0.00 | 2.33 | 2.33 | 1.362 | 0.452 | 0.501 | No | SURFACE 61 | 0.00 | 90.00 | N | ||
| SUB SURFACE 49 | KATERRATYPICALWINDOWRESIDENTIAL | 4.46 | 0.00 | 0.00 | 4.46 | 4.46 | 1.362 | 0.452 | 0.501 | No | SURFACE 86 | 90.00 | 90.00 | E | ||
| SUB SURFACE 52 | KATERRATYPICALWINDOWRESIDENTIAL | 2.33 | 0.00 | 0.00 | 2.33 | 2.33 | 1.362 | 0.452 | 0.501 | No | SURFACE 86 | 90.00 | 90.00 | E | ||
| SUB SURFACE 40 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 74 | 270.00 | 90.00 | W | ||
| SUB SURFACE 46 | KATERRATYPICALWINDOWRESIDENTIAL | 1.85 | 0.00 | 0.00 | 1.85 | 1.85 | 1.362 | 0.452 | 0.501 | No | SURFACE 78 | 270.00 | 90.00 | W | ||
| SUB SURFACE 43 | KATERRATYPICALWINDOWRESIDENTIAL | 2.23 | 0.00 | 0.00 | 2.23 | 2.23 | 1.362 | 0.452 | 0.501 | No | SURFACE 79 | 180.00 | 90.00 | S | ||
| SUB SURFACE 33 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 100 | 270.00 | 90.00 | W | ||
| SUB SURFACE 28 | KATERRATYPICALWINDOWRESIDENTIAL | 4.46 | 0.00 | 0.00 | 4.46 | 4.46 | 1.362 | 0.452 | 0.501 | No | SURFACE 101 | 0.00 | 90.00 | N | ||
| SUB SURFACE 22 | KATERRATYPICALWINDOWRESIDENTIAL | 1.44 | 0.00 | 0.00 | 1.44 | 1.44 | 1.362 | 0.452 | 0.501 | No | SURFACE 103 | 0.00 | 90.00 | N | ||
| SUB SURFACE 23 | KATERRATYPICALWINDOWRESIDENTIAL | 1.44 | 0.00 | 0.00 | 1.44 | 1.44 | 1.362 | 0.452 | 0.501 | No | SURFACE 103 | 0.00 | 90.00 | N | ||
| SUB SURFACE 31 | KATERRATYPICALWINDOWRESIDENTIAL | 2.33 | 0.00 | 0.00 | 2.33 | 2.33 | 1.362 | 0.452 | 0.501 | No | SURFACE 106 | 270.00 | 90.00 | W | ||
| SUB SURFACE 32 | KATERRATYPICALWINDOWRESIDENTIAL | 2.33 | 0.00 | 0.00 | 2.33 | 2.33 | 1.362 | 0.452 | 0.501 | No | SURFACE 106 | 270.00 | 90.00 | W | ||
| SUB SURFACE 4 | KATERRATYPICALWINDOWRESIDENTIAL | 1.14 | 0.00 | 0.00 | 1.14 | 1.14 | 1.362 | 0.452 | 0.501 | No | SURFACE 89 | 90.00 | 90.00 | E | ||
| SUB SURFACE 1 | KATERRATYPICALWINDOWRESIDENTIAL | 2.23 | 0.00 | 0.00 | 2.23 | 2.23 | 1.362 | 0.452 | 0.501 | No | SURFACE 90 | 0.00 | 90.00 | N | ||
| SUB SURFACE 7 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 91 | 90.00 | 90.00 | E | ||
| SUB SURFACE 8 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 91 | 90.00 | 90.00 | E | ||
| SUB SURFACE 9 | KATERRATYPICALWINDOWRESIDENTIAL | 3.48 | 0.00 | 0.00 | 3.48 | 3.48 | 1.362 | 0.452 | 0.501 | No | SURFACE 91 | 90.00 | 90.00 | E | ||
| SUB SURFACE 16 | KATERRATYPICALWINDOWRESIDENTIAL | 1.44 | 0.00 | 0.00 | 1.44 | 1.44 | 1.362 | 0.452 | 0.501 | No | SURFACE 97 | 0.00 | 90.00 | N | ||
| SUB SURFACE 21 | KATERRATYPICALWINDOWRESIDENTIAL | 2.33 | 0.00 | 0.00 | 2.33 | 2.33 | 1.362 | 0.452 | 0.501 | No | SURFACE 97 | 0.00 | 90.00 | N | ||
| Total or Average | 135.80 | 1.362 | 0.452 | 0.501 | ||||||||||||
| North Total or Average | 38.65 | 1.362 | 0.452 | 0.501 | ||||||||||||
| Non-North Total or Average | 97.15 | 1.362 | 0.452 | 0.501 |
| Construction | Area of One Opening [m2] | Area of Openings [m2] | Glass U-Factor [W/m2-K] | Glass SHGC | Glass Visible Transmittance | Parent Surface | |
| Total or Average | 0.00 | - | - | - |
| Construction | U-Factor with Film [W/m2-K] | U-Factor no Film [W/m2-K] | Gross Area [m2] | Parent Surface | |
| SUB SURFACE 63 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 12 |
| SUB SURFACE 66 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 3 |
| SUB SURFACE 57 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 33 |
| SUB SURFACE 60 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 23 |
| SUB SURFACE 62 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 48 |
| SUB SURFACE 65 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 39 |
| SUB SURFACE 56 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 69 |
| SUB SURFACE 59 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 59 |
| SUB SURFACE 61 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 84 |
| SUB SURFACE 64 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 75 |
| SUB SURFACE 55 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 105 |
| SUB SURFACE 58 | EXTERIOR DOOR | 1.004 | 1.181 | 1.95 | SURFACE 95 |
Report: Shading Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Sunlit Fraction| March 21 9am | March 21 noon | March 21 3pm | June 21 9am | June 21 noon | June 21 3pm | December 21 9am | December 21 noon | December 21 3pm | |
| SUB SURFACE 51 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 54 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 42 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 48 | 0.00 | 0.00 | 0.98 | 0.00 | 0.00 | 0.11 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 45 | 0.00 | 0.00 | 0.95 | 0.00 | 0.00 | 0.63 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 37 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 30 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 26 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 27 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 38 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 39 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 6 | 1.00 | 0.00 | 0.00 | 0.96 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 3 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 13 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 14 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 15 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 18 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 19 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 50 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 53 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 41 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 47 | 0.00 | 0.00 | 0.98 | 0.00 | 0.00 | 0.11 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 44 | 0.00 | 0.00 | 0.95 | 0.00 | 0.00 | 0.63 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 34 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 29 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 24 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 25 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 35 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 36 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 5 | 1.00 | 0.00 | 0.00 | 0.96 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 2 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 10 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 11 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 12 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 17 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 20 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 49 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 52 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 40 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 46 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 43 | 0.00 | 0.00 | 1.00 | 0.00 | 0.24 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 33 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 28 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 22 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 23 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 31 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 32 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 | 0.00 | 1.00 |
| SUB SURFACE 4 | 1.00 | 0.27 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 1 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 7 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 8 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 9 | 1.00 | 1.00 | 0.00 | 1.00 | 1.00 | 0.00 | 0.00 | 1.00 | 0.00 |
| SUB SURFACE 16 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| SUB SURFACE 21 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 | 0.00 |
| Name | Type | Shaded Construction | Control | Glare Control | |
| None |
Report: Lighting Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Interior Lighting| Zone | Lighting Power Density [W/m2] | Zone Area [m2] | Total Power [W] | End Use Subcategory | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Return Air Fraction | Conditioned (Y/N) | Consumption [GJ] | |
| 01_A1 LIGHTS 2 | 01_A1 | 4.1269 | 57.60 | 237.71 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 0.80 |
| 02_A1 LIGHTS 2 | 02_A1 | 4.1269 | 57.60 | 237.71 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 0.80 |
| 03_A1 LIGHTS 2 | 03_A1 | 4.1269 | 57.60 | 237.71 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 0.80 |
| 01_A2 LIGHTS 3 | 01_A2 | 3.7286 | 62.25 | 232.09 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 0.78 |
| 02_A2 LIGHTS 3 | 02_A2 | 3.7286 | 62.25 | 232.09 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 0.78 |
| 03_A2 LIGHTS 3 | 03_A2 | 3.7286 | 62.25 | 232.09 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 0.78 |
| 01_B2 LIGHTS 7 | 01_B2 | 3.2604 | 96.77 | 315.52 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 1.06 |
| 02_B2 LIGHTS 7 | 02_B2 | 3.2604 | 96.77 | 315.52 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 1.06 |
| 03_B2 LIGHTS 7 | 03_B2 | 3.2604 | 96.77 | 315.52 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 1.06 |
| 01_C1 LIGHTS 8 | 01_C1 | 3.0849 | 113.62 | 350.51 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 1.17 |
| 02_C1 LIGHTS 8 | 02_C1 | 3.0849 | 113.62 | 350.51 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 1.17 |
| 03_C1 LIGHTS 8 | 03_C1 | 3.0849 | 113.62 | 350.51 | General | MIDRISEAPARTMENT APARTMENT LIGHTDOE | 17.85 | 168.00 | 17.85 | 0.0000 | Y | 1.17 |
| Interior Lighting Total | 3.4394 | 990.72 | 3407.49 | 11.42 |
| Zone | Control Name | Daylighting Method | Control Type | Fraction Controlled | Lighting Installed in Zone [W] | Lighting Controlled [W] | |
| None |
| Total Watts | Astronomical Clock/Schedule | Schedule Name | Scheduled Hours/Week [hr] | Hours/Week > 1% [hr] | Full Load Hours/Week [hr] | Consumption [GJ] | |
| Exterior Lighting Total | 0.00 | 0.00 |
Report: Equipment Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Central Plant| Type | Nominal Capacity [W] | Nominal Efficiency [W/W] | IPLV in SI Units [W/W] | IPLV in IP Units [Btu/W-h] | |
| None |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Sensible Capacity [W] | Nominal Latent Capacity [W] | Nominal Sensible Heat Ratio | Nominal Efficiency [W/W] | Nominal Coil UA Value [W/C] | Nominal Coil Surface Area [m2] | |
| 1 SPD DX CLG COIL 4 | Coil:Cooling:DX:SingleSpeed | 4861.80 | 3393.94 | 1467.86 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 13 | Coil:Cooling:DX:SingleSpeed | 9638.61 | 6728.56 | 2910.06 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 14 | Coil:Cooling:DX:SingleSpeed | 11251.35 | 7854.38 | 3396.97 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 15 | Coil:Cooling:DX:SingleSpeed | 9772.83 | 6822.25 | 2950.58 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 5 | Coil:Cooling:DX:SingleSpeed | 8063.07 | 5628.69 | 2434.38 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 6 | Coil:Cooling:DX:SingleSpeed | 6383.80 | 4456.42 | 1927.38 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 7 | Coil:Cooling:DX:SingleSpeed | 4785.29 | 3340.53 | 1444.76 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 8 | Coil:Cooling:DX:SingleSpeed | 8063.07 | 5628.69 | 2434.38 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 9 | Coil:Cooling:DX:SingleSpeed | 9240.05 | 6450.32 | 2789.73 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 10 | Coil:Cooling:DX:SingleSpeed | 10526.44 | 7348.33 | 3178.11 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 11 | Coil:Cooling:DX:SingleSpeed | 9216.66 | 6434.00 | 2782.67 | 0.70 | 3.52 | |||
| 1 SPD DX CLG COIL 12 | Coil:Cooling:DX:SingleSpeed | 8063.07 | 5628.69 | 2434.38 | 0.70 | 3.52 |
| DX Cooling Coil Type | Standard Rated Net Cooling Capacity [W] | Standard Rated Net COP [W/W] | EER [Btu/W-h] | SEER [Btu/W-h] | IEER [Btu/W-h] | |
| 1 SPD DX CLG COIL 4 | 4707.3 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 13 | 9332.4 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 14 | 10893.9 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 15 | 9462.4 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 5 | 7806.9 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 6 | 6181.0 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 7 | 4633.3 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 8 | 7806.9 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 9 | 8946.5 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 10 | 10192.0 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 11 | 8923.9 | 3.07 | 10.47 | 10.41 | 10.78 | |
| 1 SPD DX CLG COIL 12 | 7806.9 | 3.07 | 10.47 | 10.41 | 10.78 |
| DX Cooling Coil Type | Rated Net Cooling Capacity Test A [W] | Rated Electric Power Test A [W] | Rated Net Cooling Capacity Test B [W] | Rated Electric Power Test B [W] | Rated Net Cooling Capacity Test C [W] | Rated Electric Power Test C [W] | Rated Net Cooling Capacity Test D [W] | Rated Electric Power Test D [W] | |
| 1 SPD DX CLG COIL 4 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 13 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 14 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 15 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 5 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 6 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 7 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 8 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 9 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 10 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 11 | Coil:Cooling:DX:SingleSpeed | ||||||||
| 1 SPD DX CLG COIL 12 | Coil:Cooling:DX:SingleSpeed |
| DX Heating Coil Type | High Temperature Heating (net) Rating Capacity [W] | Low Temperature Heating (net) Rating Capacity [W] | HSPF [Btu/W-h] | Region Number | |
| 1 SPD DX HTG COIL 3 | Coil:Heating:DX:SingleSpeed | 5019.1 | 2761.8 | 6.53 | 4 |
| 1 SPD DX HTG COIL 12 | Coil:Heating:DX:SingleSpeed | 9950.5 | 5475.3 | 6.54 | 4 |
| 1 SPD DX HTG COIL 13 | Coil:Heating:DX:SingleSpeed | 11615.4 | 6391.4 | 6.54 | 4 |
| 1 SPD DX HTG COIL 14 | Coil:Heating:DX:SingleSpeed | 10089.0 | 5551.5 | 6.54 | 4 |
| 1 SPD DX HTG COIL 4 | Coil:Heating:DX:SingleSpeed | 8323.9 | 4580.3 | 6.54 | 4 |
| 1 SPD DX HTG COIL 5 | Coil:Heating:DX:SingleSpeed | 6590.3 | 3626.4 | 6.54 | 4 |
| 1 SPD DX HTG COIL 6 | Coil:Heating:DX:SingleSpeed | 4940.1 | 2718.3 | 6.54 | 4 |
| 1 SPD DX HTG COIL 7 | Coil:Heating:DX:SingleSpeed | 8323.9 | 4580.3 | 6.54 | 4 |
| 1 SPD DX HTG COIL 8 | Coil:Heating:DX:SingleSpeed | 9539.0 | 5248.9 | 6.54 | 4 |
| 1 SPD DX HTG COIL 9 | Coil:Heating:DX:SingleSpeed | 10867.0 | 5979.6 | 6.54 | 4 |
| 1 SPD DX HTG COIL 10 | Coil:Heating:DX:SingleSpeed | 9514.9 | 5235.6 | 6.54 | 4 |
| 1 SPD DX HTG COIL 11 | Coil:Heating:DX:SingleSpeed | 8323.9 | 4580.3 | 6.54 | 4 |
| Type | Design Coil Load [W] | Nominal Total Capacity [W] | Nominal Efficiency [W/W] | |
| 1 SPD DX HTG COIL 3 | Coil:Heating:DX:SingleSpeed | 4861.80 | 2.93 | |
| ELEC HTG COIL 5 | Coil:Heating:Electric | 4861.80 | 1.00 | |
| 1 SPD DX HTG COIL 12 | Coil:Heating:DX:SingleSpeed | 9638.61 | 2.93 | |
| ELEC HTG COIL 14 | Coil:Heating:Electric | 9638.61 | 1.00 | |
| 1 SPD DX HTG COIL 13 | Coil:Heating:DX:SingleSpeed | 11251.35 | 2.93 | |
| ELEC HTG COIL 15 | Coil:Heating:Electric | 11251.35 | 1.00 | |
| 1 SPD DX HTG COIL 14 | Coil:Heating:DX:SingleSpeed | 9772.83 | 2.93 | |
| ELEC HTG COIL 16 | Coil:Heating:Electric | 9772.83 | 1.00 | |
| 1 SPD DX HTG COIL 4 | Coil:Heating:DX:SingleSpeed | 8063.07 | 2.93 | |
| ELEC HTG COIL 6 | Coil:Heating:Electric | 8063.07 | 1.00 | |
| 1 SPD DX HTG COIL 5 | Coil:Heating:DX:SingleSpeed | 6383.80 | 2.93 | |
| ELEC HTG COIL 7 | Coil:Heating:Electric | 6383.80 | 1.00 | |
| 1 SPD DX HTG COIL 6 | Coil:Heating:DX:SingleSpeed | 4785.29 | 2.93 | |
| ELEC HTG COIL 8 | Coil:Heating:Electric | 4785.29 | 1.00 | |
| 1 SPD DX HTG COIL 7 | Coil:Heating:DX:SingleSpeed | 8063.07 | 2.93 | |
| ELEC HTG COIL 9 | Coil:Heating:Electric | 8063.07 | 1.00 | |
| 1 SPD DX HTG COIL 8 | Coil:Heating:DX:SingleSpeed | 9240.05 | 2.93 | |
| ELEC HTG COIL 10 | Coil:Heating:Electric | 9240.05 | 1.00 | |
| 1 SPD DX HTG COIL 9 | Coil:Heating:DX:SingleSpeed | 10526.44 | 2.93 | |
| ELEC HTG COIL 11 | Coil:Heating:Electric | 10526.44 | 1.00 | |
| 1 SPD DX HTG COIL 10 | Coil:Heating:DX:SingleSpeed | 9216.66 | 2.93 | |
| ELEC HTG COIL 12 | Coil:Heating:Electric | 9216.66 | 1.00 | |
| 1 SPD DX HTG COIL 11 | Coil:Heating:DX:SingleSpeed | 8063.07 | 2.93 | |
| ELEC HTG COIL 13 | Coil:Heating:Electric | 8063.07 | 1.00 |
| Type | Total Efficiency [W/W] | Delta Pressure [pa] | Max Air Flow Rate [m3/s] | Rated Electric Power [W] | Rated Power Per Max Air Flow Rate [W-s/m3] | Motor Heat In Air Fraction | End Use | Design Day Name for Fan Sizing Peak | Date/Time for Fan Sizing Peak | |
| FAN ON OFF 5 | Fan:OnOff | 0.60 | 300.00 | 0.20 | 97.89 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 14 | Fan:OnOff | 0.60 | 300.00 | 0.39 | 194.07 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 15 | Fan:OnOff | 0.60 | 300.00 | 0.45 | 226.55 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 16 | Fan:OnOff | 0.60 | 300.00 | 0.39 | 196.78 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 6 | Fan:OnOff | 0.60 | 300.00 | 0.32 | 162.35 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 7 | Fan:OnOff | 0.60 | 300.00 | 0.26 | 128.54 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 8 | Fan:OnOff | 0.60 | 300.00 | 0.19 | 96.35 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 9 | Fan:OnOff | 0.60 | 300.00 | 0.32 | 162.35 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 10 | Fan:OnOff | 0.60 | 300.00 | 0.37 | 186.05 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 11 | Fan:OnOff | 0.60 | 300.00 | 0.42 | 211.95 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 12 | Fan:OnOff | 0.60 | 300.00 | 0.37 | 185.58 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| FAN ON OFF 13 | Fan:OnOff | 0.60 | 300.00 | 0.32 | 162.35 | 500.00 | 1.00 | General | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 |
| Type | Control | Head [pa] | Water Flow [m3/s] | Electric Power [W] | Power Per Water Flow Rate [W-s/m3] | Motor Efficiency [W/W] | |
| None |
| Type | Storage Volume [m3] | Input [W] | Thermal Efficiency [W/W] | Recovery Efficiency [W/W] | Energy Factor | |
| None |
Report: HVAC Sizing Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Zone Sensible Cooling| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| 01_A1 | 2888.33 | 3321.58 | 57.67 | 0.170 | 0.196 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.01390 | 20.27 | 0.00702 | 0.024 | -66.79 |
| 01_A2 | 3669.23 | 4219.61 | 67.79 | 0.216 | 0.249 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00927 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 01_B2 | 3791.77 | 4360.53 | 45.06 | 0.224 | 0.257 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00948 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 01_C1 | 2842.30 | 3268.65 | 28.77 | 0.168 | 0.193 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.01002 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 02_A1 | 4487.80 | 5160.97 | 89.60 | 0.265 | 0.304 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00913 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 02_A2 | 5488.08 | 6311.30 | 101.39 | 0.324 | 0.372 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00902 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 02_B2 | 6252.36 | 7190.21 | 74.30 | 0.369 | 0.424 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00909 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 02_C1 | 5474.43 | 6295.60 | 55.41 | 0.323 | 0.371 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00928 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 03_A1 | 4717.02 | 5424.58 | 94.18 | 0.278 | 0.320 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00910 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 03_A2 | 5724.80 | 6583.52 | 105.77 | 0.338 | 0.388 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00899 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 03_B2 | 6682.94 | 7685.38 | 79.42 | 0.394 | 0.453 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00906 | 20.27 | 0.00702 | 0.024 | 0.00 |
| 03_C1 | 5804.79 | 6675.51 | 58.75 | 0.342 | 0.394 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 23.90 | 23.90 | 0.00924 | 20.27 | 0.00702 | 0.024 | 0.00 |
| Calculated Design Load [W] | User Design Load [W] | User Design Load per Area [W/m2] | Calculated Design Air Flow [m3/s] | User Design Air Flow [m3/s] | Design Day Name | Date/Time Of Peak {TIMESTAMP} | Thermostat Setpoint Temperature at Peak Load [C] | Indoor Temperature at Peak Load [C] | Indoor Humidity Ratio at Peak Load [kgWater/kgAir] | Outdoor Temperature at Peak Load [C] | Outdoor Humidity Ratio at Peak Load [kgWater/kgAir] | Minimum Outdoor Air Flow Rate [m3/s] | Heat Gain Rate from DOAS [W] | |
| 01_A1 | 25.12 | 31.40 | 0.55 | 0.002 | 0.024 | ANCHORAGEELMENDORFANNHUM_N99.6CONDNSDPMCDB | 1/21 01:40:00 | 23.90 | 23.90 | 0.00600 | -23.70 | 0.00024 | 0.024 | -66.41 |
| 01_A2 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 | |
| 01_B2 | 141.24 | 176.54 | 1.82 | 0.008 | 0.024 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 05:00:00 | 21.10 | 21.10 | 0.01587 | -26.00 | 0.00035 | 0.024 | 0.00 |
| 01_C1 | 101.74 | 127.18 | 1.12 | 0.006 | 0.024 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 05:00:00 | 21.10 | 21.10 | 0.01587 | -26.00 | 0.00035 | 0.024 | 0.00 |
| 02_A1 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 | |
| 02_A2 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 | |
| 02_B2 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 | |
| 02_C1 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 | |
| 03_A1 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 | |
| 03_A2 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 | |
| 03_B2 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 | |
| 03_C1 | 0.00 | 0.00 | 0.00 | 0.000 | 0.325 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 0.00 | 21.10 | 0.00800 | -26.00 | 0.00035 | 0.024 | 0.00 |
| Calculated cooling [m3/s] | User cooling [m3/s] | Calculated heating [m3/s] | User heating [m3/s] | Adjusted cooling [m3/s] | Adjusted heating [m3/s] | Adjusted main [m3/s] | Calculated Heating Air Flow Ratio [] | User Heating Air Flow Ratio [] | |
| AIR LOOP HVAC 1 | 0.20 | 0.20 | 0.02 | 0.02 | 0.1958 | 0.1958 | 0.1958 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 10 | 0.39 | 0.39 | 0.32 | 0.32 | 0.3881 | 0.3881 | 0.3881 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 11 | 0.45 | 0.45 | 0.32 | 0.32 | 0.4531 | 0.4531 | 0.4531 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 12 | 0.39 | 0.39 | 0.32 | 0.32 | 0.3936 | 0.3936 | 0.3936 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 2 | 0.25 | 0.25 | 0.32 | 0.32 | 0.3247 | 0.3247 | 0.3247 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 3 | 0.26 | 0.26 | 0.02 | 0.02 | 0.2571 | 0.2571 | 0.2571 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 4 | 0.19 | 0.19 | 0.02 | 0.02 | 0.1927 | 0.1927 | 0.1927 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 5 | 0.30 | 0.30 | 0.32 | 0.32 | 0.3247 | 0.3247 | 0.3247 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 6 | 0.37 | 0.37 | 0.32 | 0.32 | 0.3721 | 0.3721 | 0.3721 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 7 | 0.42 | 0.42 | 0.32 | 0.32 | 0.4239 | 0.4239 | 0.4239 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 8 | 0.37 | 0.37 | 0.32 | 0.32 | 0.3712 | 0.3712 | 0.3712 | 1.0000 | 0.3000 |
| AIR LOOP HVAC 9 | 0.32 | 0.32 | 0.32 | 0.32 | 0.3247 | 0.3247 | 0.3247 | 1.0000 | 0.3000 |
| Previous Design Volume Flow Rate [m3/s] | Algorithm Volume Flow Rate [m3/s] | Coincident Design Volume Flow Rate [m3/s] | Coincident Size Adjusted | Peak Sizing Period Name | Peak Day into Period {TIMESTAMP}[day] | Peak Hour Of Day {TIMESTAMP}[hr] | Peak Step Start Minute {TIMESTAMP}[min] | |
| None |
| Coil Type | HVAC Type | HVAC Name | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | |
| 1 SPD DX CLG COIL 4 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 1 | 4861.805 | 3393.944 | 0.195785 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 4861.80 | 4861.80 | 0.195785 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 12.0527 | 23.90 | 0.01389814 | 74.1182 | 3321.58 | 0.00 | 4858.75 | 3397.54 |
| 1 SPD DX HTG COIL 3 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 1 | 4861.805 | 4861.805 | 0.195785 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 4861.80 | 4861.80 | 0.195785 | -23.70 | -24.18 | 0.00023755 | 16.70 | 13.12 | 0.00800000 | -23.70 | 0.00023755 | -24.18 | 12.0527 | 23.90 | 0.00599560 | 32.3765 | 31.40 | 0.00 | 4867.70 | 4867.70 |
| ELEC HTG COIL 5 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 1 | 4861.805 | 4861.805 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 4861.80 | 4861.80 | 0.195785 | -23.70 | -24.18 | 0.00023755 | 16.70 | 13.12 | 0.00800000 | -23.70 | 0.00023755 | -24.18 | 12.0527 | 23.90 | 0.00599560 | 32.3765 | 31.40 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 13 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 10 | 9638.615 | 6728.555 | 0.388147 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 9638.61 | 9638.61 | 0.388147 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 6.0795 | 23.90 | 0.00899487 | 48.3518 | 6583.52 | 0.00 | 9632.55 | 6735.68 |
| 1 SPD DX HTG COIL 12 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 10 | 9638.615 | 9638.615 | 0.388147 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9638.61 | 9638.61 | 0.388147 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 6.0795 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 9650.30 | 9650.30 |
| ELEC HTG COIL 14 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 10 | 9638.615 | 9638.615 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9638.61 | 9638.61 | 0.388147 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 6.0795 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 14 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 11 | 11251.348 | 7854.377 | 0.453092 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 11251.35 | 11251.35 | 0.453092 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 5.2081 | 23.90 | 0.00905580 | 48.6729 | 7685.38 | 0.00 | 11244.27 | 7862.69 |
| 1 SPD DX HTG COIL 13 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 11 | 11251.348 | 11251.348 | 0.453092 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 11251.35 | 11251.35 | 0.453092 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 5.2081 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 11264.99 | 11264.99 |
| ELEC HTG COIL 15 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 11 | 11251.348 | 11251.348 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 11251.35 | 11251.35 | 0.453092 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 5.2081 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 15 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 12 | 9772.830 | 6822.249 | 0.393552 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 13:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 9772.83 | 9772.83 | 0.393552 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 5.9960 | 23.90 | 0.00923945 | 49.6454 | 6675.51 | 0.00 | 9766.68 | 6829.47 |
| 1 SPD DX HTG COIL 14 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 12 | 9772.830 | 9772.830 | 0.393552 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9772.83 | 9772.83 | 0.393552 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 5.9960 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 9784.68 | 9784.68 |
| ELEC HTG COIL 16 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 12 | 9772.830 | 9772.830 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9772.83 | 9772.83 | 0.393552 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 5.9960 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 5 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 2 | 8063.070 | 5628.694 | 0.324700 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 8063.07 | 8063.07 | 0.324700 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 7.2674 | 23.90 | 0.00927091 | 49.8147 | 4219.61 | 0.00 | 8058.00 | 5634.65 |
| 1 SPD DX HTG COIL 4 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 2 | 8063.070 | 8063.070 | 0.324700 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 0.324700 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 7.2674 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 8072.85 | 8072.85 |
| ELEC HTG COIL 6 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 2 | 8063.070 | 8063.070 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 0.324700 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 7.2674 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 6 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 3 | 6383.796 | 4456.421 | 0.257075 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 6383.80 | 6383.80 | 0.257075 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 9.1792 | 23.90 | 0.00947578 | 50.8963 | 4360.53 | 0.00 | 6379.78 | 4461.14 |
| 1 SPD DX HTG COIL 5 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 3 | 6383.796 | 6383.796 | 0.257075 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 | 6383.80 | 6383.80 | 0.257075 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 9.1792 | 21.10 | 0.01586837 | 100.0000 | 176.54 | 0.00 | 6391.54 | 6391.54 |
| ELEC HTG COIL 7 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 3 | 6383.796 | 6383.796 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 | 6383.80 | 6383.80 | 0.257075 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 9.1792 | 21.10 | 0.01586837 | 100.0000 | 176.54 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 7 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 4 | 4785.289 | 3340.530 | 0.192704 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 4785.29 | 4785.29 | 0.192704 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 12.2454 | 23.90 | 0.01001518 | 53.7476 | 3268.65 | 0.00 | 4782.28 | 3344.07 |
| 1 SPD DX HTG COIL 6 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 4 | 4785.289 | 4785.289 | 0.192704 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 | 4785.29 | 4785.29 | 0.192704 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 12.2454 | 21.10 | 0.01586797 | 100.0000 | 127.18 | 0.00 | 4791.09 | 4791.09 |
| ELEC HTG COIL 8 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 4 | 4785.289 | 4785.289 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 | 4785.29 | 4785.29 | 0.192704 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 12.2454 | 21.10 | 0.01586797 | 100.0000 | 127.18 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 8 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 5 | 8063.070 | 5628.694 | 0.324700 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 8063.07 | 8063.07 | 0.324700 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 7.2674 | 23.90 | 0.00913102 | 49.0740 | 5160.97 | 0.00 | 8058.00 | 5634.65 |
| 1 SPD DX HTG COIL 7 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 5 | 8063.070 | 8063.070 | 0.324700 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 0.324700 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 7.2674 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 8072.85 | 8072.85 |
| ELEC HTG COIL 9 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 5 | 8063.070 | 8063.070 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 0.324700 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 7.2674 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 9 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 6 | 9240.048 | 6450.322 | 0.372097 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 9240.05 | 9240.05 | 0.372097 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 6.3417 | 23.90 | 0.00901574 | 48.4622 | 6311.30 | 0.00 | 9234.24 | 6457.15 |
| 1 SPD DX HTG COIL 8 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 6 | 9240.048 | 9240.048 | 0.372097 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9240.05 | 9240.05 | 0.372097 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 6.3417 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 9251.25 | 9251.25 |
| ELEC HTG COIL 10 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 6 | 9240.048 | 9240.048 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9240.05 | 9240.05 | 0.372097 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 6.3417 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 10 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 7 | 10526.437 | 7348.329 | 0.423900 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 10526.44 | 10526.44 | 0.423900 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 5.5667 | 23.90 | 0.00909388 | 48.8747 | 7190.21 | 0.00 | 10519.82 | 7356.11 |
| 1 SPD DX HTG COIL 9 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 7 | 10526.437 | 10526.437 | 0.423900 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 10526.44 | 10526.44 | 0.423900 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 5.5667 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 10539.20 | 10539.20 |
| ELEC HTG COIL 11 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 7 | 10526.437 | 10526.437 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 10526.44 | 10526.44 | 0.423900 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 5.5667 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 11 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 8 | 9216.664 | 6433.999 | 0.371155 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 13:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 9216.66 | 9216.66 | 0.371155 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 6.3578 | 23.90 | 0.00928379 | 49.8802 | 6295.60 | 0.00 | 9210.87 | 6440.81 |
| 1 SPD DX HTG COIL 10 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 8 | 9216.664 | 9216.664 | 0.371155 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9216.66 | 9216.66 | 0.371155 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 6.3578 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 9227.84 | 9227.84 |
| ELEC HTG COIL 12 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 8 | 9216.664 | 9216.664 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9216.66 | 9216.66 | 0.371155 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 6.3578 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
| 1 SPD DX CLG COIL 12 | Coil:Cooling:DX:SingleSpeed | AirLoopHVAC | AIR LOOP HVAC 9 | 8063.070 | 5628.694 | 0.324700 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 8063.07 | 8063.07 | 0.324700 | 20.27 | 13.58 | 0.00702465 | 12.80 | 12.04 | 0.00850000 | 20.27 | 0.00702465 | 13.58 | 7.2674 | 23.90 | 0.00910064 | 48.9131 | 5424.58 | 0.00 | 8058.00 | 5634.65 |
| 1 SPD DX HTG COIL 11 | COIL:HEATING:DX:SINGLESPEED | AirLoopHVAC | AIR LOOP HVAC 9 | 8063.070 | 8063.070 | 0.324700 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 0.324700 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 7.2674 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 8072.85 | 8072.85 |
| ELEC HTG COIL 13 | COIL:HEATING:ELECTRIC | AirLoopHVAC | AIR LOOP HVAC 9 | 8063.070 | 8063.070 | -999.0 | -999.0 | -999.000 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 0.324700 | -26.00 | -26.00 | 0.00035410 | 16.70 | 13.12 | 0.00800000 | -26.00 | 0.00035410 | -26.00 | 7.2674 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 |
Report: Coil Sizing Details
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Coils| Coil Type | Coil Location | HVAC Type | HVAC Name | Zone Name(s) | System Sizing Method Concurrence | System Sizing Method Capacity | System Sizing Method Air Flow | Autosized Coil Capacity? | Autosized Coil Airflow? | Autosized Coil Water Flow? | OA Pretreated prior to coil inlet? | Coil Final Gross Total Capacity [W] | Coil Final Gross Sensible Capacity [W] | Coil Final Reference Air Volume Flow Rate [m3/s] | Coil Final Reference Plant Fluid Volume Flow Rate [m3/s] | Coil U-value Times Area Value [W/K] | Terminal Unit Reheat Coil Multiplier | DX Coil Capacity Increase Ratio from Too Low Flow/Capacity Ratio | DX Coil Capacity Decrease Ratio from Too High Flow/Capacity Ratio | Moist Air Heat Capacity [J/kg-K] | Dry Air Heat Capacity [J/kg-K] | Standard Air Density Adjusted for Elevation [kg/m3] | Supply Fan Name for Coil | Supply Fan Type for Coil | Supply Fan Maximum Air Volume Flow Rate [m3/s] | Supply Fan Maximum Air Mass Flow Rate [kg/s] | Plant Name for Coil | Plant Fluid Specific Heat Capacity [J/kg-K] | Plant Fluid Density [kg/m3] | Plant Maximum Fluid Mass Flow Rate [kg/s] | Plant Design Fluid Return Temperature [C] | Plant Design Fluid Supply Temperature [C] | Plant Design Fluid Temperature Difference [deltaC] | Plant Design Capacity [W] | Coil Capacity Percentage of Plant Design Capacity [%] | Coil Fluid Flow Rate Percentage of Plant Design Flow Rate [%] | Design Day Name at Sensible Ideal Loads Peak | Date/Time at Sensible Ideal Loads Peak | Design Day Name at Total Ideal Loads Peak | Date/Time at Total Ideal Loads Peak | Design Day Name at Air Flow Ideal Loads Peak | Date/Time at Air Flow Ideal Loads Peak | Coil Total Capacity at Ideal Loads Peak [W] | Coil Sensible Capacity at Ideal Loads Peak [W] | Coil Off-Rating Capacity Modifier at Ideal Loads Peak [ ] | Coil Air Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Coil Entering Air Drybulb at Ideal Loads Peak [C] | Coil Entering Air Wetbulb at Ideal Loads Peak [C] | Coil Entering Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Leaving Air Drybulb at Ideal Loads Peak [C] | Coil Leaving Air Wetbulb at Ideal Loads Peak [C] | Coil Leaving Air Humidity Ratio at Ideal Loads Peak [C] | Coil Leaving Air Enthalpy at Ideal Loads Peak [J/KG-K] | Coil Plant Fluid Mass Flow Rate at Ideal Loads Peak [kg/s] | Coil Entering Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Leaving Plant Fluid Temperature at Ideal Loads Peak [C] | Coil Plant Fluid Temperature Difference at Ideal Loads Peak [deltaC] | Supply Fan Air Heat Gain at Ideal Loads Peak [W] | Coil and Fan Net Total Capacity at Ideal Loads Peak [W] | Outdoor Air Drybulb at Ideal Loads Peak [C] | Outdoor Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Outdoor Air Wetbulb at Ideal Loads Peak [C] | Outdoor Air Volume Flow Rate at Ideal Loads Peak [m3/s] | Outdoor Air Flow Percentage at Ideal Loads Peak [%] | System Return Air Drybulb at Ideal Loads Peak [C] | System Return Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Drybulb at Ideal Loads Peak [C] | Zone Air Humidity Ratio at Ideal Loads Peak [KGWATER/KGDRYAIR] | Zone Air Relative Humidity at Ideal Loads Peak [%] | Zone Sensible Heat Gain at Ideal Loads Peak [W] | Zone Latent Heat Gain at Ideal Loads Peak [W] | Coil Total Capacity at Rating Conditions [W] | Coil Sensible Capacity at Rating Conditions [W] | Coil Air Mass Flow Rate at Rating Conditions [kg/s] | Coil Entering Air Drybulb at Rating Conditions [C] | Coil Entering Air Wetbulb at Rating Conditions [C] | Coil Entering Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Entering Air Enthalpy at Rating Conditions [J/KG-K] | Coil Leaving Air Drybulb at Rating Conditions [C] | Coil Leaving Air Wetbulb at Rating Conditions [C] | Coil Leaving Air Humidity Ratio at Rating Conditions [KGWATER/KGDRYAIR] | Coil Leaving Air Enthalpy at Rating Conditions [J/KG-K] | |
| 1 SPD DX CLG COIL 4 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 1 | 01_A1 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 4861.805 | 3393.944 | 0.195785 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 5 | Fan:OnOff | 0.195785 | 0.23414076 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 4861.80 | 4861.80 | 1.0000 | 0.23414076 | 0.195785 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4861.80 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 12.0527 | 23.90 | 0.01389814 | 23.90 | 0.01389814 | 74.1182 | 3321.58 | 0.00 | 4858.75 | 3397.54 | 0.22487078 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 3 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 1 | 01_A1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 4861.805 | 4861.805 | 0.195785 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 5 | Fan:OnOff | 0.195785 | 0.23414076 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 4861.80 | 4861.80 | 1.0000 | 0.23414076 | 0.195785 | -23.70 | -24.18 | 0.00023755 | -23231.1 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4861.80 | -23.70 | 0.00023755 | -24.18 | 0.02359737 | 12.0527 | 23.80 | 0.00599560 | 23.90 | 0.00599560 | 32.3765 | 31.40 | 0.00 | 4867.70 | 4867.70 | 0.23000342 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 5 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 1 | 01_A1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 4861.805 | 4861.805 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 5 | Fan:OnOff | 0.195785 | 0.23414076 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 4861.80 | 4861.80 | 1.0000 | 0.23414076 | 0.195785 | -23.70 | -24.18 | 0.00023755 | -23231.1 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4861.80 | -23.70 | 0.00023755 | -24.18 | 0.02359737 | 12.0527 | 23.80 | 0.00599560 | 23.90 | 0.00599560 | 32.3765 | 31.40 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 13 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 10 | 03_A2 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 9638.615 | 6728.555 | 0.388147 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 14 | Fan:OnOff | 0.388147 | 0.46418823 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 9638.61 | 9638.61 | 1.0000 | 0.46418823 | 0.388147 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9638.61 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 6.0795 | 23.90 | 0.00899487 | 23.90 | 0.00899487 | 48.3518 | 6583.52 | 0.00 | 9632.55 | 6735.68 | 0.44581032 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 12 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 10 | 03_A2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 9638.615 | 9638.615 | 0.388147 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 14 | Fan:OnOff | 0.388147 | 0.46418823 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9638.61 | 9638.61 | 1.0000 | 0.46418823 | 0.388147 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9638.61 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 6.0795 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 9650.30 | 9650.30 | 0.45598588 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 14 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 10 | 03_A2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 9638.615 | 9638.615 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 14 | Fan:OnOff | 0.388147 | 0.46418823 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9638.61 | 9638.61 | 1.0000 | 0.46418823 | 0.388147 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9638.61 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 6.0795 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 14 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 11 | 03_B2 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 11251.348 | 7854.377 | 0.453092 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 15 | Fan:OnOff | 0.453092 | 0.54185624 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 11251.35 | 11251.35 | 1.0000 | 0.54185624 | 0.453092 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 11251.35 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 5.2081 | 23.90 | 0.00905580 | 23.90 | 0.00905580 | 48.6729 | 7685.38 | 0.00 | 11244.27 | 7862.69 | 0.52040334 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 13 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 11 | 03_B2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 11251.348 | 11251.348 | 0.453092 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 15 | Fan:OnOff | 0.453092 | 0.54185624 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 11251.35 | 11251.35 | 1.0000 | 0.54185624 | 0.453092 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 11251.35 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 5.2081 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 11264.99 | 11264.99 | 0.53228147 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 15 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 11 | 03_B2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 11251.348 | 11251.348 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 15 | Fan:OnOff | 0.453092 | 0.54185624 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 11251.35 | 11251.35 | 1.0000 | 0.54185624 | 0.453092 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 11251.35 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 5.2081 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 15 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 12 | 03_C1 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 9772.830 | 6822.249 | 0.393552 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 16 | Fan:OnOff | 0.393552 | 0.47065193 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 13:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 14:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 9772.83 | 9772.83 | 1.0000 | 0.47065193 | 0.393552 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9772.83 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 5.9960 | 23.90 | 0.00923945 | 23.90 | 0.00923945 | 49.6454 | 6675.51 | 0.00 | 9766.68 | 6829.47 | 0.45201812 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 14 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 12 | 03_C1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 9772.830 | 9772.830 | 0.393552 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 16 | Fan:OnOff | 0.393552 | 0.47065193 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9772.83 | 9772.83 | 1.0000 | 0.47065193 | 0.393552 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9772.83 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 5.9960 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 9784.68 | 9784.68 | 0.46233537 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 16 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 12 | 03_C1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 9772.830 | 9772.830 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 16 | Fan:OnOff | 0.393552 | 0.47065193 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9772.83 | 9772.83 | 1.0000 | 0.47065193 | 0.393552 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9772.83 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 5.9960 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 5 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 2 | 01_A2 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 8063.070 | 5628.694 | 0.324700 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 6 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 7.2674 | 23.90 | 0.00927091 | 23.90 | 0.00927091 | 49.8147 | 4219.61 | 0.00 | 8058.00 | 5634.65 | 0.37293741 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 4 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 2 | 01_A2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 8063.070 | 8063.070 | 0.324700 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 6 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 7.2674 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 8072.85 | 8072.85 | 0.38144965 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 6 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 2 | 01_A2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 8063.070 | 8063.070 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 6 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 7.2674 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 6 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 3 | 01_B2 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 6383.796 | 4456.421 | 0.257075 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 7 | Fan:OnOff | 0.257075 | 0.30743868 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 6383.80 | 6383.80 | 1.0000 | 0.30743868 | 0.257075 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6383.80 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 9.1792 | 23.90 | 0.00947578 | 23.90 | 0.00947578 | 50.8963 | 4360.53 | 0.00 | 6379.78 | 4461.14 | 0.29526673 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 5 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 3 | 01_B2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 6383.796 | 6383.796 | 0.257075 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 7 | Fan:OnOff | 0.257075 | 0.30743868 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 | 6383.80 | 6383.80 | 1.0000 | 0.30743868 | 0.257075 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6383.80 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 9.1792 | 21.10 | 0.01586837 | 21.10 | 0.01586837 | 100.0000 | 176.54 | 0.00 | 6391.54 | 6391.54 | 0.30200614 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 7 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 3 | 01_B2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 6383.796 | 6383.796 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 7 | Fan:OnOff | 0.257075 | 0.30743868 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 03:20:00 | 6383.80 | 6383.80 | 1.0000 | 0.30743868 | 0.257075 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 6383.80 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 9.1792 | 21.10 | 0.01586837 | 21.10 | 0.01586837 | 100.0000 | 176.54 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 7 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 4 | 01_C1 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 4785.289 | 3340.530 | 0.192704 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 8 | Fan:OnOff | 0.192704 | 0.23045582 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 4785.29 | 4785.29 | 1.0000 | 0.23045582 | 0.192704 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4785.29 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 12.2454 | 23.90 | 0.01001518 | 23.90 | 0.01001518 | 53.7476 | 3268.65 | 0.00 | 4782.28 | 3344.07 | 0.22133173 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 6 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 4 | 01_C1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 4785.289 | 4785.289 | 0.192704 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 8 | Fan:OnOff | 0.192704 | 0.23045582 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 | 4785.29 | 4785.29 | 1.0000 | 0.23045582 | 0.192704 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4785.29 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 12.2454 | 21.10 | 0.01586797 | 21.10 | 0.01586797 | 100.0000 | 127.18 | 0.00 | 4791.09 | 4791.09 | 0.22638360 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 8 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 4 | 01_C1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 4785.289 | 4785.289 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 8 | Fan:OnOff | 0.192704 | 0.23045582 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 04:20:00 | 4785.29 | 4785.29 | 1.0000 | 0.23045582 | 0.192704 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 4785.29 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 12.2454 | 21.10 | 0.01586797 | 21.10 | 0.01586797 | 100.0000 | 127.18 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 8 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 5 | 02_A1 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 8063.070 | 5628.694 | 0.324700 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 9 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 14:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 7.2674 | 23.90 | 0.00913102 | 23.90 | 0.00913102 | 49.0740 | 5160.97 | 0.00 | 8058.00 | 5634.65 | 0.37293741 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 7 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 5 | 02_A1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 8063.070 | 8063.070 | 0.324700 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 9 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 7.2674 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 8072.85 | 8072.85 | 0.38144965 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 9 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 5 | 02_A1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 8063.070 | 8063.070 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 9 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 7.2674 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 9 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 6 | 02_A2 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 9240.048 | 6450.322 | 0.372097 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 10 | Fan:OnOff | 0.372097 | 0.44499357 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 9240.05 | 9240.05 | 1.0000 | 0.44499357 | 0.372097 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9240.05 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 6.3417 | 23.90 | 0.00901574 | 23.90 | 0.00901574 | 48.4622 | 6311.30 | 0.00 | 9234.24 | 6457.15 | 0.42737561 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 8 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 6 | 02_A2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 9240.048 | 9240.048 | 0.372097 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 10 | Fan:OnOff | 0.372097 | 0.44499357 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9240.05 | 9240.05 | 1.0000 | 0.44499357 | 0.372097 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9240.05 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 6.3417 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 9251.25 | 9251.25 | 0.43713039 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 10 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 6 | 02_A2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 9240.048 | 9240.048 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 10 | Fan:OnOff | 0.372097 | 0.44499357 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9240.05 | 9240.05 | 1.0000 | 0.44499357 | 0.372097 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9240.05 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 6.3417 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 10 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 7 | 02_B2 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 10526.437 | 7348.329 | 0.423900 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 11 | Fan:OnOff | 0.423900 | 0.50694507 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 10526.44 | 10526.44 | 1.0000 | 0.50694507 | 0.423900 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 10526.44 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 5.5667 | 23.90 | 0.00909388 | 23.90 | 0.00909388 | 48.8747 | 7190.21 | 0.00 | 10519.82 | 7356.11 | 0.48687436 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 9 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 7 | 02_B2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 10526.437 | 10526.437 | 0.423900 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 11 | Fan:OnOff | 0.423900 | 0.50694507 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 10526.44 | 10526.44 | 1.0000 | 0.50694507 | 0.423900 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 10526.44 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 5.5667 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 10539.20 | 10539.20 | 0.49798719 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 11 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 7 | 02_B2 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 10526.437 | 10526.437 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 11 | Fan:OnOff | 0.423900 | 0.50694507 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 10526.44 | 10526.44 | 1.0000 | 0.50694507 | 0.423900 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 10526.44 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 5.5667 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 11 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 8 | 02_C1 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 9216.664 | 6433.999 | 0.371155 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 12 | Fan:OnOff | 0.371155 | 0.44386742 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 13:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 13:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 9216.66 | 9216.66 | 1.0000 | 0.44386742 | 0.371155 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9216.66 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 6.3578 | 23.90 | 0.00928379 | 23.90 | 0.00928379 | 49.8802 | 6295.60 | 0.00 | 9210.87 | 6440.81 | 0.42629404 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 10 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 8 | 02_C1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 9216.664 | 9216.664 | 0.371155 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 12 | Fan:OnOff | 0.371155 | 0.44386742 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9216.66 | 9216.66 | 1.0000 | 0.44386742 | 0.371155 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9216.66 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 6.3578 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 9227.84 | 9227.84 | 0.43602414 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 12 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 8 | 02_C1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 9216.664 | 9216.664 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 12 | Fan:OnOff | 0.371155 | 0.44386742 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 9216.66 | 9216.66 | 1.0000 | 0.44386742 | 0.371155 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 9216.66 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 6.3578 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | |
| 1 SPD DX CLG COIL 12 | Coil:Cooling:DX:SingleSpeed | AirLoop | AirLoopHVAC | AIR LOOP HVAC 9 | 03_A1 | Non-Coincident | CoolingDesignCapacity | N/A | Yes | Yes | unknown | No | 8063.070 | 5628.694 | 0.324700 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1017.8985 | 1004.8586 | 1.1959 | FAN ON OFF 13 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 18:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSENTHMDB | 7/21 14:00:00 | ANCHORAGEELMENDORFANNCLG.4CONDNSDBMWB | 7/21 19:00:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | 20.27 | 13.58 | 0.00702465 | 38206.1 | 12.80 | 12.04 | 0.00850000 | 34322.2 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | 20.27 | 0.00702465 | 13.58 | 0.02359737 | 7.2674 | 23.90 | 0.00910064 | 23.90 | 0.00910064 | 48.9131 | 5424.58 | 0.00 | 8058.00 | 5634.65 | 0.37293741 | 26.67 | 19.44 | 0.01117891 | 55307.7 | 11.87 | 11.84 | 0.00863119 | 33700.9 | |
| 1 SPD DX HTG COIL 11 | COIL:HEATING:DX:SINGLESPEED | AirLoop | AirLoopHVAC | AIR LOOP HVAC 9 | 03_A1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | Yes | unknown | No | 8063.070 | 8063.070 | 0.324700 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 13 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 7.2674 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | 8072.85 | 8072.85 | 0.38144965 | 21.11 | 15.55 | 0.00874580 | 43428.1 | 41.84 | 22.21 | 0.00874580 | 64591.7 | |
| ELEC HTG COIL 13 | COIL:HEATING:ELECTRIC | AirLoop | AirLoopHVAC | AIR LOOP HVAC 9 | 03_A1 | Non-Coincident | HeatingDesignCapacity | N/A | Yes | No | unknown | No | 8063.070 | 8063.070 | -999.0 | -999.0 | -999.000 | -999.0000 | 1.00000 | 1.00000 | 1019.7116 | 1004.8586 | 1.1959 | FAN ON OFF 13 | Fan:OnOff | 0.324700 | 0.38831123 | -999.0000 | -999.0000 | -999.0 | -999.00 | -999.00 | -999.00 | -999.00 | -999.0000 | -999.0 | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | unknown | unknown | ANCHORAGEELMENDORFANNHTG99.6CONDNSDB | 1/21 00:10:00 | 8063.07 | 8063.07 | 1.0000 | 0.38831123 | 0.324700 | -26.00 | -26.00 | 0.00035410 | -25257.4 | 16.70 | 13.12 | 0.00800000 | 37036.7 | -999.0 | -999.00 | -999.00 | -999.00 | 0.000 | 8063.07 | -26.00 | 0.00035410 | -26.00 | 0.02359737 | 7.2674 | 21.10 | 0.00800000 | 21.10 | 0.00800000 | 51.0480 | 0.00 | 0.00 | -999.00 | -999.00 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 | -999.00 | -999.00 | -999.0 | -999.0 |
Report: System Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Economizer| High Limit Shutoff Control | Minimum Outdoor Air [m3/s] | Maximum Outdoor Air [m3/s] | Return Air Temp Limit | Return Air Enthalpy Limit | Outdoor Air Temperature Limit [C] | Outdoor Air Enthalpy Limit [C] | |
| None |
| Controller:MechanicalVentilation Name | Outdoor Air Per Person [m3/s-person] | Outdoor Air Per Area [m3/s-m2] | Outdoor Air Per Zone [m3/s] | Outdoor Air ACH [ach] | Outdoor Air Method | Outdoor Air Schedule Name | Air Distribution Effectiveness in Cooling Mode | Air Distribution Effectiveness in Heating Mode | Air Distribution Effectiveness Schedule Name | |
| 01_A1 | CONTROLLER MECHANICAL VENTILATION 1 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 01_A2 | CONTROLLER MECHANICAL VENTILATION 2 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 01_B2 | CONTROLLER MECHANICAL VENTILATION 3 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 01_C1 | CONTROLLER MECHANICAL VENTILATION 4 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 02_A1 | CONTROLLER MECHANICAL VENTILATION 5 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 02_A2 | CONTROLLER MECHANICAL VENTILATION 6 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 02_B2 | CONTROLLER MECHANICAL VENTILATION 7 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 02_C1 | CONTROLLER MECHANICAL VENTILATION 8 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 03_A1 | CONTROLLER MECHANICAL VENTILATION 9 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 03_A2 | CONTROLLER MECHANICAL VENTILATION 10 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 03_B2 | CONTROLLER MECHANICAL VENTILATION 11 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 | |
| 03_C1 | CONTROLLER MECHANICAL VENTILATION 12 | 0.000000 | 0.000000 | 0.023597 | 0.000000 | Sum | ALWAYS_ON | 1.00 | 1.00 |
| Winter Clothes [hr] | Summer Clothes [hr] | Summer or Winter Clothes [hr] | |
| 01_A1 | 5318.67 | 8756.83 | 5318.67 |
| 01_A2 | 6270.33 | 8754.50 | 6270.33 |
| 01_B2 | 5328.50 | 8759.33 | 5328.50 |
| 01_C1 | 5013.50 | 8760.00 | 5013.50 |
| 02_A1 | 3157.50 | 8600.00 | 3156.83 |
| 02_A2 | 4806.33 | 8247.83 | 4760.33 |
| 02_B2 | 3115.83 | 8541.83 | 3115.83 |
| 02_C1 | 2325.50 | 8534.00 | 2323.17 |
| 03_A1 | 3283.83 | 8548.33 | 3283.83 |
| 03_A2 | 3726.67 | 8525.67 | 3726.67 |
| 03_B2 | 3296.83 | 8483.17 | 3296.83 |
| 03_C1 | 2593.33 | 8464.00 | 2591.83 |
| Facility | 6419.00 | 8760.00 | 6372.33 |
| During Heating [hr] | During Cooling [hr] | During Occupied Heating [hr] | During Occupied Cooling [hr] | |
| 01_A1 | 701.33 | 0.00 | 701.33 | 0.00 |
| 01_A2 | 634.83 | 0.00 | 634.83 | 0.00 |
| 01_B2 | 718.67 | 0.00 | 718.67 | 0.00 |
| 01_C1 | 896.50 | 0.00 | 896.50 | 0.00 |
| 02_A1 | 672.17 | 0.00 | 672.17 | 0.00 |
| 02_A2 | 645.83 | 0.00 | 645.83 | 0.00 |
| 02_B2 | 681.67 | 0.00 | 681.67 | 0.00 |
| 02_C1 | 709.67 | 0.00 | 709.67 | 0.00 |
| 03_A1 | 675.00 | 0.00 | 675.00 | 0.00 |
| 03_A2 | 669.50 | 0.00 | 669.50 | 0.00 |
| 03_B2 | 679.17 | 0.00 | 679.17 | 0.00 |
| 03_C1 | 706.33 | 0.00 | 706.33 | 0.00 |
| Facility | 907.50 | 0.00 | 907.50 | 0.00 |
Report: Outdoor Air Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Average Outdoor Air During Occupied Hours| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| 01_A1 | 1.14 | 1.55 | 193.12 | 0.448 | 0.000 | 0.000 | 0.000 |
| 01_A2 | 1.14 | 1.55 | 208.70 | 0.415 | 0.000 | 0.000 | 0.000 |
| 01_B2 | 1.81 | 2.47 | 324.46 | 0.267 | 0.000 | 0.000 | 0.000 |
| 01_C1 | 2.49 | 3.39 | 380.95 | 0.227 | 0.000 | 0.000 | 0.000 |
| 02_A1 | 1.14 | 1.55 | 193.12 | 0.449 | 0.000 | 0.000 | 0.000 |
| 02_A2 | 1.14 | 1.55 | 208.70 | 0.415 | 0.000 | 0.000 | 0.000 |
| 02_B2 | 1.81 | 2.47 | 324.46 | 0.267 | 0.000 | 0.000 | 0.000 |
| 02_C1 | 2.49 | 3.39 | 380.95 | 0.228 | 0.000 | 0.000 | 0.000 |
| 03_A1 | 1.14 | 1.55 | 193.12 | 0.449 | 0.000 | 0.000 | 0.000 |
| 03_A2 | 1.14 | 1.55 | 208.70 | 0.415 | 0.000 | 0.000 | 0.000 |
| 03_B2 | 1.81 | 2.47 | 324.46 | 0.267 | 0.000 | 0.000 | 0.000 |
| 03_C1 | 2.49 | 3.39 | 380.95 | 0.228 | 0.000 | 0.000 | 0.000 |
| Average Number of Occupants | Nominal Number of Occupants | Zone Volume [m3] | Mechanical Ventilation [ach] | Infiltration [ach] | AFN Infiltration [ach] | Simple Ventilation [ach] | |
| 01_A1 | 1.14 | 1.55 | 193.12 | 0.426 | 0.000 | 0.000 | 0.000 |
| 01_A2 | 1.14 | 1.55 | 208.70 | 0.392 | 0.000 | 0.000 | 0.000 |
| 01_B2 | 1.81 | 2.47 | 324.46 | 0.254 | 0.000 | 0.000 | 0.000 |
| 01_C1 | 2.49 | 3.39 | 380.95 | 0.217 | 0.000 | 0.000 | 0.000 |
| 02_A1 | 1.14 | 1.55 | 193.12 | 0.419 | 0.000 | 0.000 | 0.000 |
| 02_A2 | 1.14 | 1.55 | 208.70 | 0.386 | 0.000 | 0.000 | 0.000 |
| 02_B2 | 1.81 | 2.47 | 324.46 | 0.251 | 0.000 | 0.000 | 0.000 |
| 02_C1 | 2.49 | 3.39 | 380.95 | 0.214 | 0.000 | 0.000 | 0.000 |
| 03_A1 | 1.14 | 1.55 | 193.12 | 0.414 | 0.000 | 0.000 | 0.000 |
| 03_A2 | 1.14 | 1.55 | 208.70 | 0.382 | 0.000 | 0.000 | 0.000 |
| 03_B2 | 1.81 | 2.47 | 324.46 | 0.247 | 0.000 | 0.000 | 0.000 |
| 03_C1 | 2.49 | 3.39 | 380.95 | 0.211 | 0.000 | 0.000 | 0.000 |
Report: Object Count Summary
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Surfaces by Class| Total | Outdoors | |
| Wall | 84 | 66 |
| Floor | 12 | 4 |
| Roof | 12 | 4 |
| Internal Mass | 0 | 0 |
| Building Detached Shading | 0 | 0 |
| Fixed Detached Shading | 0 | 0 |
| Window | 54 | 54 |
| Door | 12 | 12 |
| Glass Door | 12 | 12 |
| Shading | 18 | 18 |
| Overhang | 0 | 0 |
| Fin | 0 | 0 |
| Tubular Daylighting Device Dome | 0 | 0 |
| Tubular Daylighting Device Diffuser | 0 | 0 |
| Count | |
| HVAC Air Loops | 12 |
| Conditioned Zones | 12 |
| Unconditioned Zones | 0 |
| Supply Plenums | 0 |
| Return Plenums | 0 |
| Count | |
| IDF Objects | 0 |
| Defaulted Fields | 0 |
| Fields with Defaults | 0 |
| Autosized Fields | 0 |
| Autosizable Fields | 0 |
| Autocalculated Fields | 0 |
| Autocalculatable Fields | 0 |
Report: Energy Meters
For: Entire Facility
Timestamp: 2018-06-04 13:40:50
Annual and Peak Values - Electricity| Electricity Annual Value [GJ] | Electricity Minimum Value [W] | Timestamp of Minimum {TIMESTAMP} | Electricity Maximum Value [W] | Timestamp of Maximum {TIMESTAMP} | |
| Electricity:Facility | 311.20 | 2837.20 | 02-JAN-03:10 | 35586.64 | 16-DEC-19:10 |
| Electricity:Building | 94.62 | 826.40 | 01-JAN-03:10 | 5235.52 | 01-JAN-18:10 |
| Electricity:Zone:01_A1 | 7.40 | 67.13 | 01-JAN-03:10 | 394.20 | 01-JAN-18:10 |
| InteriorLights:Electricity | 11.42 | 68.15 | 01-JAN-00:10 | 1090.40 | 01-JAN-19:10 |
| InteriorLights:Electricity:Zone:01_A1 | 0.80 | 4.75 | 01-JAN-00:10 | 76.07 | 01-JAN-19:10 |
| General:InteriorLights:Electricity | 11.42 | 68.15 | 01-JAN-00:10 | 1090.40 | 01-JAN-19:10 |
| Electricity:Zone:02_A1 | 7.40 | 67.13 | 01-JAN-03:10 | 394.20 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:02_A1 | 0.80 | 4.75 | 01-JAN-00:10 | 76.07 | 01-JAN-19:10 |
| Electricity:Zone:03_A1 | 7.40 | 67.13 | 01-JAN-03:10 | 394.20 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:03_A1 | 0.80 | 4.75 | 01-JAN-00:10 | 76.07 | 01-JAN-19:10 |
| Electricity:Zone:01_A2 | 7.38 | 67.02 | 01-JAN-03:10 | 392.68 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:01_A2 | 0.78 | 4.64 | 01-JAN-00:10 | 74.27 | 01-JAN-19:10 |
| Electricity:Zone:02_A2 | 7.38 | 67.02 | 01-JAN-03:10 | 392.68 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:02_A2 | 0.78 | 4.64 | 01-JAN-00:10 | 74.27 | 01-JAN-19:10 |
| Electricity:Zone:03_A2 | 7.38 | 67.02 | 01-JAN-03:10 | 392.68 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:03_A2 | 0.78 | 4.64 | 01-JAN-00:10 | 74.27 | 01-JAN-19:10 |
| Electricity:Zone:01_B2 | 8.18 | 69.96 | 01-JAN-03:10 | 461.55 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:01_B2 | 1.06 | 6.31 | 01-JAN-00:10 | 100.97 | 01-JAN-19:10 |
| Electricity:Zone:02_B2 | 8.18 | 69.96 | 01-JAN-03:10 | 461.55 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:02_B2 | 1.06 | 6.31 | 01-JAN-00:10 | 100.97 | 01-JAN-19:10 |
| Electricity:Zone:03_B2 | 8.18 | 69.96 | 01-JAN-03:10 | 461.55 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:03_B2 | 1.06 | 6.31 | 01-JAN-00:10 | 100.97 | 01-JAN-19:10 |
| Electricity:Zone:01_C1 | 8.58 | 71.36 | 01-JAN-03:10 | 496.74 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:01_C1 | 1.17 | 7.01 | 01-JAN-00:10 | 112.16 | 01-JAN-19:10 |
| Electricity:Zone:02_C1 | 8.58 | 71.36 | 01-JAN-03:10 | 496.74 | 01-JAN-18:10 |
| InteriorLights:Electricity:Zone:02_C1 | 1.17 | 7.01 | 01-JAN-00:10 | 112.16 | 01-JAN-19:10 |
| Electricity:Zone:03_C1 | 8.58 | 71.36 | 01-JAN-03:10 | 496.74 | 01-JAN-18:10 |